<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>LTHW - Boiler shunt - Boiler bypass pump no 1 not operation when switchen on to hand at the panel.&nbsp;</li>
	<li>LTHW - 1st Floor VT - Pump replaced differential pressuer switch disconnected.</li>
	<li>LTHW - East/West wing - Pump&nbsp;replaced differential pressuer switch disconnected.</li>
	<li>LTHW - Boiler Shunt - Boiler by pass pump no1 not operational when switched onto hand at the panel differential switch disconnected.</li>
	<li>LTHW - 1ST Floor VT - 1st floor VT pump no2 showing no differential across the pump set before going into fault at the panel.&nbsp;</li>
	<li>LTHW East/Wing VT - East/West VT pump no1 run lamp was lit when switched to hand however it was not operational.&nbsp;</li>
	<li>Site to be left clean and tidy.</li>
</ul>
