<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>To install barriers to working area.&nbsp;</li>
	<li>Engie to isolate all smoke heads,&nbsp;</li>
	<li>Area to be out of use when we are working in the room.&nbsp;</li>
	<li>3 phase socket to be installed surface mounted, with surface mounted isolator 4mm SWA supply pulled in from distribution board using existing containment.&nbsp;</li>
	<li>20amp RCBO to be installed in DB for 30ma Protection.</li>
	<li>Roughly 42 meter run to DB using existing containment.&nbsp;</li>
	<li>Working area to be left as found before works commence.&nbsp;</li>
	<li>NIC certification to be issued to client after works complete.&nbsp;</li>
	<li>Site to be left clean and tidy.</li>
</ul>
