<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>To carry out project to scope below.</li>
</ul>

<p><span style="text-autospace:none"><b>&nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; Item 1</b></span></p>

<ul>
	<li>
	<p><span style="text-autospace:none"><b>UPS SYSTEM</b></span></p>

	<p><span style="text-autospace:none">1 x Vertiv APM 9 UPS fitted with 2 x 30kW / 30kVA, configured as 2 x 30kW power Modules. The</span></p>

	<p><span style="text-autospace:none">UPS can be configured to 60kW N+1 or 90kW Capacity in the future if required. Fitted in the existing</span></p>

	<p style="margin-bottom:11px">UPS Room with new input and output breakers in the existing bypass panel.</p>

	<p><span style="text-autospace:none"><b>Item 2</b></span></p>

	<p><span style="text-autospace:none"><b>BATTERIES &amp; RACKS</b></span></p>

	<p><span style="text-autospace:none">To provide 2 Strings of Fiamm Batteries in a cladded rack to deliver 6 minutes autonomy at full load per</span></p>

	<p><span style="text-autospace:none">power module, we have worked on 2 x 30kW IT Load and standard 1.67vpc cut off.</span></p>

	<p><span style="text-autospace:none">We have designed these for 6 minutes at full load and end of life.</span></p>

	<p><span style="text-autospace:none">Battery Dimensions: 1130mmW X 830mmD X 2100mmH</span></p>

	<p style="margin-bottom:11px">Battery Weight: 1104kG</p>

	<p><span style="text-autospace:none"><b>BATTERY CIRCUIT BREAKER</b></span></p>

	<p><span style="text-autospace:none">To deliver and install a 90kW Rated APM Battery Circuit Breaker. Breaker fitted with 3 x Sets of</span></p>

	<p><span style="text-autospace:none">String Fuses 2 sets to be fitted with 315 amp rated fuses for two strings. When further modules are</span></p>

	<p style="margin-bottom:11px">fitted the DC fuse rating can be reduced.</p>

	<p><span style="text-autospace:none"><b>PANEL MODIFICATIONS</b></span></p>

	<p><span style="text-autospace:none">We need to change out two of the breakers on the input from 63 amp to 160 amp (3 pole and bolted</span></p>

	<p><span style="text-autospace:none">neutral) and a non auto 160amp return from the UPS. This enables the UPS Units to be fully rated at</span></p>

	<p><span style="text-autospace:none">100kW load in the future.</span></p>

	<p style="margin-bottom:11px">When the panel is shutdown we will make the modifications to the Panel and integrate the new breakers.</p>

	<p><span style="text-autospace:none"><b>Item 5</b></span></p>

	<p><span style="text-autospace:none"><b>MATERIALS</b></span></p>

	<p><span style="text-autospace:none">The list of the electrical materials for the installation of the New UPS Systems.</span></p>

	<p><span style="text-autospace:none"><b>Code:</b></span></p>

	<p>&nbsp;</p>

	<p><span style="text-autospace:none"><b>Product Description: Product type: QTY:</b></span></p>

	<p><span style="text-autospace:none">&nbsp;Cable HO7BN4-F (6385TQ) 50mm2 36</span></p>

	<p><span style="text-autospace:none">&nbsp;Cable HO7BN4-F (6387TQ) 1.5mm2 12</span></p>

	<p><span style="text-autospace:none">XLPE/SWA/5/25 Cable Cable XLPE/SWA 5core 25mm2</span></p>

	<p><span style="text-autospace:none">Labour Man Day Normal Working Hours NWH 8</span></p>

	<p><span style="text-autospace:none">Labour Man Day Weekend Working Hours WWH 8</span></p>

	<p style="margin-bottom:11px">1 night Hotel &amp; Subsistence ACC 8</p>

	<p><span style="text-autospace:none"><b>Item 6</b></span></p>

	<p><span style="text-autospace:none"><b>DELIVERY, OFFLOADING &amp; POSITIONING</b></span></p>

	<p><span style="text-autospace:none">Delivery to site and positioning of the equipment, we will then meet the delivery on site and carry out</span></p>

	<p style="margin-bottom:11px">the installation. All deliveries will be done outside normal working hours.</p>

	<p><span style="text-autospace:none"><b>Item 7</b></span></p>

	<p><span style="text-autospace:none"><b>BMS WORKS</b></span></p>

	<p><span style="text-autospace:none">We included to connect the UPS&rsquo;s to the existing BMS without any programming.</span></p>

	<p style="margin-bottom:11px">&nbsp;</p>

	<p style="margin-bottom:11px"><b>Item 8</b></p>

	<p><span style="text-autospace:none"><b>LOADBANK</b></span></p>

	<p style="margin-bottom:11px">To provide a 100kW Crestchic Loadbank for one week on site with suitably rated cables.</p>

	<p><span style="text-autospace:none"><b>Item 9</b></span></p>

	<p><span style="text-autospace:none"><b>OLD EQUIPMENT REMOVAL</b></span></p>

	<p><span style="text-autospace:none">To remove the old UPS and associated equipment from site for recycling and certified disposal.</span></p>

	<p><span style="text-autospace:none">&bull; Attending site and carrying out all site inductions as required.</span></p>

	<p><span style="text-autospace:none">&bull; Dismantle / strip out 6 x 40kVA UPS and associated battery cabinets</span></p>

	<p><span style="text-autospace:none">&bull; Place suitable floor protection along all manoeuvring routes</span></p>

	<p><span style="text-autospace:none">&bull; Manoeuvre the units out of the Comms Room and out of the building</span></p>

	<p><span style="text-autospace:none">&bull; Further removal of the equipment form site for recycling.</span></p>

	<p><span style="text-autospace:none"><b>Item 10</b></span></p>

	<p><span style="text-autospace:none"><b>COMMISIONING AND ON SITE TESTING</b></span></p>

	<p><span style="text-autospace:none">Commissioning of the above systems described in the quotation above outside normal working hours.</span></p>

	<p><span style="text-autospace:none">To our standard specification or other approved with CBRE,&nbsp;</span></p>

	<p><span style="text-autospace:none">Including Loadbank load testing and battery discharge test</span></p>

	<p><span style="text-autospace:none"><b>Item 11</b></span></p>

	<p><span style="text-autospace:none"><b>LOADBANK</b></span></p>

	<p><span style="text-autospace:none">To provide a 100kW Crestchic Loadbank for one week on site with suitably rated cables.</span></p>

	<p><span style="text-autospace:none">We would recommend that the Generator is run during these tests. To prove the system in its entirety.</span></p>

	<p><span style="text-autospace:none"><b>Item 12</b></span></p>

	<p><span style="text-autospace:none"><b>NORMAL WORKING HOURS</b></span></p>

	<p><span style="text-autospace:none">To provide Qualified Electricians during Normal Working Hours.</span></p>

	<p><span style="text-autospace:none"><b>Item 13</b></span></p>

	<p><span style="text-autospace:none"><b>OUTSIDE NORMAL WORKING HOURS</b></span></p>

	<p><span style="text-autospace:none">To provide Qualified Electricians during Outside Normal Working Hours.</span></p>

	<p><span style="text-autospace:none"><b>Item 14</b></span></p>

	<p><span style="text-autospace:none"><b>PROJECT MANAGEMENT / SITE SUPERVISION</b></span></p>

	<p><span style="text-autospace:none">To provide onsite project management of the site including finalisation of the as fitted drawings.</span></p>

	<p style="margin-bottom:11px">To provide CSCS&nbsp;Site Supervision throughout our works.</p>

	<p><span style="text-autospace:none"><b>Item 15</b></span></p>

	<p><span style="text-autospace:none"><b>BATTERY BUILD &amp; DC CABLING</b></span></p>

	<p><span style="text-autospace:none">To carry out the Battery Build and DC Cabling of New UPS System.</span></p>

	<p><span style="text-autospace:none">&bull; Build Battery Racks and position on plinth and cut floor for legs.</span></p>

	<p><span style="text-autospace:none">&bull; Mount Battery Circuit Breaker on the End of the Rack.</span></p>

	<p><span style="text-autospace:none">&bull; Mount BCB near UPS taking the two battery connections.</span></p>

	<p><span style="text-autospace:none">&bull; Load the Fiamm Batteries to the rack 2 x 40 Batteries</span></p>

	<p><span style="text-autospace:none">&bull; Link the batteries (leaving safety links out)</span></p>

	<p><span style="text-autospace:none">&bull; Torque to Fiamm Recommended Settings</span></p>

	<p><span style="text-autospace:none">&bull; Connect the String Take offs to the BCB Fuse Sections(fuses removed)</span></p>

	<p><span style="text-autospace:none">&bull; Install 4 Meters of Cable tray between UPS and BCB</span></p>

	<p><span style="text-autospace:none">&bull; Install 5 Meters of 1 x 50mm Per Pole TQ Single Cores Terminate at each end (Between UPS</span></p>

	<p><span style="text-autospace:none">&amp; BCB &amp; BCB to each Rack)</span></p>

	<p style="margin-bottom:11px">&bull; Install 4 x 4 Core Battery Control Cable between UPS and BCB</p>

	<p><span style="text-autospace:none"><b>Item 16</b></span></p>

	<p><span style="text-autospace:none"><b>DC STRIP OUT</b></span></p>

	<p><span style="text-autospace:none">To break down the existing batteries and position into bins for safe disposal.</span></p>

	<p><span style="text-autospace:none"><b>Item 17</b></span></p>

	<p><span style="text-autospace:none"><b>AC STRIP OUT</b></span></p>

	<p><span style="text-autospace:none">To break down the existing electrical equipment for removal.</span></p>

	<p><span style="text-autospace:none"><b>Item 18</b></span></p>

	<p><span style="text-autospace:none"><b>TRANSPORT / ACCOMODATION</b></span></p>

	<p><span style="text-autospace:none">We have included for all transportation and accommodation for the duration of the project.</span></p>

	<p><span style="text-autospace:none"><b>Item 19</b></span></p>

	<p><span style="text-autospace:none"><b>LEAD REBATE</b></span></p>

	<p><span style="text-autospace:none">We have a lead rebate that we have passed back as a negative on the cost of this project.</span></p>

	<p><span style="text-autospace:none">We will have the 6 x 64 Yuasa SWL 1100FR batteries (384 in total).</span></p>

	<p><span style="text-autospace:none"><b>Item 20</b></span></p>

	<p><span style="text-autospace:none"><b>CERTIFICATION</b></span></p>

	<p><span style="text-autospace:none">We will provide an NICEIC / ECA Certificate for all the cabling that we perform. We will be</span></p>

	<p><span style="text-autospace:none">sending UK trained 17th Edition trained Electricians who work within Critical Environments.</span></p>

	<p><span style="text-autospace:none"><b>Item 21</b></span></p>

	<p style="margin-bottom:11px"><b>SITE LABELING</b></p>

	<p><span style="text-autospace:none"><b>Item 22</b></span></p>

	<p><span style="text-autospace:none"><b>HEALTH &amp; SAFETY</b></span></p>

	<p><span style="text-autospace:none">To provide Documentation, Signage etc</span></p>

	<p><span style="text-autospace:none">GDC will appoint a dedicated Health and Safety representative who will</span></p>

	<p><span style="text-autospace:none">have the following responsibilities: -</span></p>

	<p><span style="text-autospace:none">&bull; Review all available information about the proposed project</span></p>

	<p><span style="text-autospace:none">&bull; Produce Method Statements and Risk Assessments for their work during the Construction</span></p>

	<p><span style="text-autospace:none">Phase and send to the Principal Contractor for review and approval prior to commencement</span></p>

	<p><span style="text-autospace:none">of work on site</span></p>

	<p><span style="text-autospace:none">Ensure all work undertaken is compliant with Health and Safety regulations</span></p>

	<p><span style="text-autospace:none"><b>Item 23</b></span></p>

	<p><span style="text-autospace:none"><b>ELECTRICAL TESTING</b></span></p>

	<p><span style="text-autospace:none">GDC will supply Vertiv the Electrical certificate to prove the AC Electrical Installation before</span></p>

	<p><span style="text-autospace:none">the UPS is energised.</span></p>

	<p><span style="text-autospace:none"><b>Item 24</b></span></p>

	<p><span style="text-autospace:none"><b>O&amp;M&rsquo;s</b></span></p>

	<p style="margin-bottom:11px">Provide O &amp; M Manual</p>
	</li>
	<li>On completion leave work area in clean and tidy condition.</li>
</ul>
