<p>Upon our attendance we have identified that the external rainwater downpipe drains directly onto the roof above the toilet. We believe this leads to a vast amount of water to run onto the roof leading to water seeping through the brickwork and entering the ceiling void. In order to alleviate the leaks experienced we propose the following remedial works:</p><p>1. Adjoin a new elbow and downpipe onto the existing pipe and re-direct to the ground.</p><p>2. Re-direct pipe to a drain if available in the immediate vicinity, if one is not available&nbsp;build a soak away&nbsp;with pea single, hopper and grate.</p><p>3. Renew the flashing band along the toilet roof.</p><p>4. Apply bitumen specific primer and paint waterproofing compound.</p><p>Our total cost to carry out the above stated works shall be: &pound;1,320.00</p><p>Labour: &pound;840.00</p><p>Materials: &pound;300.00</p><p>Access equipment: &pound;100.00</p><p>Plant &amp; Hire: &pound;80.00</p>