<ul><li>Operatives to apply protective sheeting to work routes and working areas.</li><li>Operatives to carry out fire stopping and easement of doors as listed below:</li><li><p>Fire stopping required for any and all breaches in fire resisting walls, floors and ceilings caused by cabling, pipes etc to maintain effective fire resistance between floors and compartments, this refers to;</p><p>1. Ground floor cupboard near flat 49 - hold in fire-boarding</p><p>2. Third floor electrical cupboard near flat 41 - various issues including door frame</p><p>3. Third floor electrical cupboard near flat 40 - cables into void</p><p>4. Second floor electrical cupboard near flat 29 - cables into void</p><p>&nbsp;</p><p>Please carry out a survey is to be identify all areas where fire resisting construction has been compromised or is not of an adequate standard.</p><p>&nbsp;</p><p>All breaches to be identified and a minimum of 1 hour fire stopping carried out.&nbsp; Please carry out all remedial works and provide a certificate of compliance.</p><p>Please provide a push bar to open sign for the fire exit adjacent to flat 43.</p><p>Please also check all fire doors in premises for general condition including intumescent strips, cold smoke seals and operation of self-closers.</p><p>Check all fire exits in premises for general condition and operation.</p><p>Examples of issues noted;</p><p>1. Third floor near flat 33 - fire doors not closing effectively</p><p>2. Second floor hear flat 26 - fire doors not closing effectively - sound deadening pads fixed to frame.</p></li><li>Site to be left clean and tidy.</li></ul><p>Our total cost to carry out the above works in normal working hours shall be &pound;2,558.00</p><p>Breakdown:</p><p>Labour: &pound;1,820.00</p><p>Materials: &pound;738.00</p>