<ul><li>To attend site to repair AC unit on the 2nd floor.</li><li>When attended to survey noticed there was no power on the indoor unit and the fuse had blown on the outdoor unit. Changed fuse and the indoor unit started running for 5 minutes then had blown again. The issue is with the outdoor fan and PCB which requires replacing.</li><li>AC unit on the outdoor unit was left isolated.</li><li>To&nbsp;re-attend to replace the controller PCB assembly, inverter PCB assembly, fan motor &amp; rubber mountings and fan propellor blades.</li><li>To test and inspect air conditioning unit is left in correct, working order.</li><li>Site to be left clean and tidy.</li></ul><p>Our total cost to carry out the above works in normal working hours shall be</p>