<ul><li>Operatives to apply protective sheeting to work routes and working areas.</li><li>Electrical supply to be installed ready for the AC units to be installed.</li><li>Supply &amp; install Mitsubishi Heavy Industries air conditioning system based on heat load calculation.</li><li>B215 Small Office (&gt;7.6kw) 1no: 10kW Heat Pump (Cooling &amp; Heating) Wall Mount Unit (1PH)&ldquo;served by&rdquo; outdoor unit wall mounted to side wall low level.</li><li>B215 Telecoms Rm (&gt;16kw) 2no: 14kW Heat Pump (Cooling &amp; Heating) Under Ceiling Units (3PH)&nbsp;&ldquo;served by&rdquo; outdoor unit wall mounted to side wall low level.</li><li>B132 Telecoms Rm (&gt;19kw) 1no: 14kW Heat Pump (Cooling &amp; Heating) Under Ceiling Unit (3PH) &ldquo;served by&rdquo; outdoor unit floor standing to side wall low level.</li><li>Site to be left clean and tidy.</li></ul><p><strong>Project Notes</strong></p><p>The heat calc varies in what&nbsp; have proposed/calculated, for example in the small office I have quoted a 10kW unit although my calc is around 7.6kW, the reason is I have had to guess the heat load of the cabinets on site as it is unknown, however the existing unit sizes (we are replacing) are the same as I have quoted so they obviously want more duty.</p><p>On &ldquo;building 132&rdquo; the above sentence is untrue is, as this currently only has a 4.5kW unit and I calculated around 19kW (with 3kW pushed on for cabinets) but have actually quoted a 14kW unit, if I was to go with the same pessimism they applied in the other building I would install 2no 10kWs or 14kWs, it really is difficult to see how they ended up with only a 4.5kW though?</p><p>Efficient inverter systems quoted as they are more environmentally friendly lowering running costs &amp; extending system life.</p><p>Evaporator condensate drainage via pumps to local waste or external drainage/roof. No condenser tray/pump/housing allowed for.</p><p>Control via hard wired wall remotes. All pipework to be exposed on new cable tray. Cabling &amp; condensate would be attached to the same.</p><p>Core holes (excluding concrete core drilling) allowed for.</p><p>Any license applications etc. are the duty of the client.</p><p>FGAS Certification included for within this quotation.</p><p>Our total cost to carry out the above works in normal working hours shall be &pound;30,673.00</p><p>Breakdown:</p><p>Labour: &pound;7,280.00</p><p>Materials: &pound;20,893.00</p><p>Plant &amp; Machinery: &pound;1,500.00</p><p>Waste: &pound;1,000.00</p>