<ul><li>&nbsp;3 Phase Consumer unit has 12 way board&nbsp;Will need updating so RCBO can be installed into the consumer unit</li><li>11 x metal-clad double socketsTo be installed in&nbsp;20mm&nbsp;galvanised&nbsp;conduit and wired in 2.5mm cable, 32 amp breaker. &nbsp;Also to pick up ring main in offices</li><li>&nbsp;1 x 13 amp metal-clad spur for water heater.To be installed 20mm conduit and wire in 4 mm, 16 amp breaker&nbsp;</li><li>3 x 13 amp metal-clad spur for heaterTo be installed in 20mm conduit, wired in 4 mm cable and on a 20 amp breaker</li><li>2 x13 amp metal-clad spur for the fire alam and CCTV</li><li>Change 4 lamps for the 5ft fluoresscent</li><li>Install 2 fire Exit sign from the ceiling with a metal chains</li><li>This will include a full testing and inspection certificate</li></ul>