<ul>
	<li>To register the installation with IFCC portal.</li>
	<li>To attend site and undertake all required inductions.</li>
	<li>To obtain all required permits and permissions.</li>
	<li>To install protection to all required areas in the form of correx and low tack tape / carpet protector.</li>
	<li>To sympathetically uplift all required carpet tiles and set aside for reinstatement.</li>
	<li>To uplift floor tiles either side of the area requiring fire stopping and set aside for reinstatement.</li>
	<li>To prepare the required area for fire stopping.</li>
	<li>To install fire batts rated to 60 minutes.</li>
	<li>To seal with Intumescent mastic rated to 60 minutes.</li>
	<li>To label installation.</li>
	<li>To undertake housekeeping to the area clearing all generated waste and debris.</li>
	<li>To reinstate previously uplifted floor tiles and carpet tiles.</li>
	<li>To uplift all installed protection.</li>
	<li>To undertake housekeeping</li>
	<li>To obtain approval and sign off.&nbsp;</li>
	<li>Upon completion to issue certification.</li>
</ul>

<p>As per issued scope works to be within:</p>

<p>S&amp;TC store room - LO-17</p>

<p>S&amp;TC workshop office - LO- 06</p>

<p>Maintainers Office - LO-07</p>

<p>Signalling Equipment room (SER) - LO-30</p>

<p>Central Equipment room (CER) - LO29</p>

<p>Control Room - L2-27</p>

<p>NR Equipment room - LO-20</p>

<p>Incident room - L2-30</p>

<p>Print room - L2-32</p>

<p>Intumescent fire batts and seals to be Firetherm Tremco 2 - 1200mm x 600mm x70mm.</p>

<p>Tested&nbsp;at Exova BM TRADA to BSEN1366-3 and BS476 Pt20/21/22. Accredited by Warrington Fire- Certificate number CF 580</p>

<p>&nbsp;</p>

<p><strong>Note</strong><br />
To limit impact on occupants and day to day undertakings works are programmed at one room per out of hours shift to ensure minimal impact.<br />
No storage is accounted for on site, all plant tools and materials will be delivered, utilised&nbsp;and removed per shift.&nbsp;<br />
As discussed with site management additional fire stopping to be confirmed and additional costs forwarded.&nbsp;</p>

<p>&nbsp;</p>
