<p><strong>Q6185 scope of works.</strong></p><p>&nbsp;</p><p>&nbsp;</p><p>Automated door closers.</p><p>Closers to be installed by others.</p><p>&nbsp;</p><ol><li>The method of running a SUPPLY for the automatic doors would be to:</li><li>Install containment between doors and local distribution board (2&rdquo; cable tray fixed direct to ceiling slab)</li><li>Install single plasterboard boxes near where closers will be located.</li><li>Run 2.5mm fp200 (check spec of closers first) from DB and plasterboard boxes.</li><li>Install 16a RCBO within distribution board.</li><li>Dead test.</li><li>Terminate both spurs.</li><li>Terminate cable within DB to RCBO.</li><li>Complete live test.</li></ol><p>&nbsp;</p><p>This job should take one electrician and one operative 3 days.</p><p>&nbsp;</p><p>The materials for this job would be as followed:</p><p>&nbsp;</p><p>36m 2&rdquo; cable tray</p><p>1x&nbsp;&nbsp;&nbsp; 2&rdquo; cable tray T</p><p>1x&nbsp;&nbsp;&nbsp; 50m 2.5mm fp200</p><p>1x&nbsp;&nbsp;&nbsp; 16a Merlin Gerin RCBO</p><p>500x penny washers</p><p>1x&nbsp;&nbsp;&nbsp;&nbsp; tub red plugs and screws</p><p>4x&nbsp;&nbsp;&nbsp;&nbsp; 20mm stuffing glands.</p><p>2x&nbsp;&nbsp;&nbsp;&nbsp; 13a spurs with neon.</p><p>1x&nbsp;&nbsp;&nbsp;&nbsp; 1m 3mm earth sleeving.</p><p>1x&nbsp;&nbsp;&nbsp;&nbsp; 100 pack of 100mm metal cable ties.</p><p>&nbsp;</p><p>Tools required will be:</p><p>&nbsp;</p><p>Electrician tools.</p><p>8 tread step ladder.</p><p>&nbsp;</p>