<ul><li>Operatives attended on 24th August.</li><li>Plumber found IPS panel to wash hand basins broken and w/c door removed.</li><li>Plumber cut out 1m section and renewed 2&quot; pipework with two 2&quot; Ts to urinals.</li><li>Plumber re-fixed IPS&nbsp;panel by drilling new holes as requested by client to make safe.</li><li>Plumber rehung w/c door by using a bolt from a upright panel.</li><li>Plumber found leak to w/c pans.</li><li>Plumber removed pans and repaired leak to cistern syphon.&nbsp; This leak has been going on for a while and has caused the floor to go rotten to a point where the pans are sinking into the wooden floor and the fixings are pulling out.&nbsp; Plumber has refixed pans as best as possible but has&nbsp;advised the client to tell the workers to be careful when they use but is up to them to deem if safe to use.&nbsp;&nbsp;Water has gone right under the lino flooring and into the hall way.&nbsp; This floor will need to be replaced to guarantee a proper fixing for pans.</li></ul><p><strong>Breakdown</strong></p><p>Labour: &pound;110.00 (5 hours)</p><p>Materials: &pound;86.98&nbsp;</p><p>Our total cost to carry out the above works in&nbsp;normal working hours shall be</p>