<ul><li>Operatives to attend 2 call outs to investigate the disconnection of 3 no lighting columns down by the main site and to look into into a faulty RCD on the light fitting.</li><li>Operatives disconnected and removed fuses from 3 no lightning columns to allow civil engineers to remove these from the ground.</li><li>Operatives removed and replaced for a new 20 light fitting and re-terminated it into the existing circuit, the issue was found to be it was tripping due to water ingress.</li><li>All works was checked and completed as per instruction from client.</li><li>Site to be left clean and tidy.</li></ul><p>Labour : &nbsp; &nbsp; &nbsp; &nbsp; &nbsp;&pound;280.00</p><p>Materials: &nbsp; &nbsp; &nbsp; &nbsp;&pound; 96.00</p><p>Our total cost to carry out the above works in / out of normal working hours shall be</p>