<p>Attended site on 24/5/18&nbsp;</p><ul><li>Attended site to investigate issue with AC unit on the 2nd floor not working.</li><li>Discovered no power on indoor unit. Fuse had blown also on the outdoor unit.</li><li>Upon attendance changed fuse and indoor unit and it started running for 5 minutes then had blown again.</li><li>Issue with outdoor fan and PCB needs replacing.</li><li>Site to be left clean and tidy.</li></ul><p>Our total cost to carry out the above works in normal working hours shall be</p>