<p><strong>SCOPE OF WORKS - 4 no. partitions to be installed (1 partition per transformer room)</strong></p><ul><li>Operatives to attend site and sign in.</li><li>All operatives to read and sign RAMS.</li><li>All materials to be transported to work areas.</li><li>Floor to ceiling non-fire partitions in rear space behind existing cage (left in situ)</li><li>Fabrication of 2no wooden steps including hazard colour stair nosings. (per transformer room)</li><li>1 no. door per wall to egress position.(per transformer room)</li><li>Decoration of accessible partition sides to white paint finish, access to cage side not possible.(per transformer room)</li><li>Fabrication &amp; installation of air transfer square/rigid ductwork to as installed discharge weatherproof louvers (no plant/dampers allowed for/required).</li></ul><p><strong>Our total cost to carry out the above works in normal working hours shall be &pound;15,489.60+VAT</strong></p><p>Breakdown</p><p>Labour - &pound;9,600.00</p><p>Materials - &pound;5,889.60</p><p><strong>SCOPE OF WORKS - &nbsp;installation of 4 no. single phase AC units. (1 no. unit per transformer room)</strong></p><ul><li>Operatives to attend site and sign in.</li><li>All operatives to read and sign RAMS.</li><li>All materials to be transported to work areas.</li><li>Supply &amp; install Mitsubishi Heavy Industries air conditioning systems based on large heat load allowance.</li><li>Supply and install 4 no.12.5kW Heat Pump (Cooling &amp; Heating) Under Ceiling Unit (1 no. unit per transformer room)</li><li>Supply and install 4 no.12.5kW condensing unit floor mounted to local partitioned space.&nbsp;(1 no. unit per transformer room)</li><li>Efficient inverter systems quoted as they are more environmentally friendly lowering running costs &amp; extending system life.</li><li>Evaporator condensate drainage via wall mounted peristaltic pump (external to unit) discharged to local boiler room floor drainage/hopper.</li><li>Control via hard-wired remote control local to unit (position&nbsp;TBC).&nbsp;</li><li>Existing weather-proof air-transfer&nbsp;louvres&nbsp;to be retained &amp; condensing unit air discharge to be site as close to this&nbsp;louvre&nbsp;as possible.</li><li>As&nbsp;louvre&nbsp;is existing for the purpose of this quote validity we assume the&nbsp;louvre&nbsp;provides adequate free air-flow to prevent re-circulation issues.</li><li>Smoke detection local to the evaporators should be relocated by others a minimum of 1M away from the air-outlet of unit to comply with&nbsp;BS5839-1:2013.</li><li>We recommend the transformer rear&nbsp;500x500mm&nbsp;ventilation opening currently against the gate/grid wall is provided with a means of free discharge ducting transition though any new partition entirely to the existing weatherproof&nbsp;louvre, failure to do so will aside from potential damage to the transformer create re-circulation between the condenser/evaporator for which a partition is to be constructed to avoid.( not costed for)</li><li>Pipework to be run surface (black in&nbsp;colour) on new&nbsp;50mm&nbsp;galvanised&nbsp;tray.</li><li>2 no&nbsp;core holes (excluding concrete core drilling) allowed for condensate. (fire stopping included within cost)</li><li>Site to be left clean and tidy.</li></ul><p><strong>Our total cost to carry out the above works in normal working hours shall be &pound;21,408.75+VAT</strong></p><p>Breakdown</p><p>Labour&nbsp;- &pound;6,000.00</p><p>Materials - &pound;14,808.75</p><p>Access Materials - &pound;600.00</p><p>&nbsp;</p><p><strong>SCOPE OF WORKS -&nbsp;electrical supplies for AC units.</strong></p><ul><li>Operatives to attend site and sign in.</li><li>All operatives to read and sign RAMS.</li><li>All materials to be transported to work areas.</li><li>2 no. sub main to be installed from existing switch panel to new distribution board locations. ( it is assumed that the existing switch panel has spare ways for new supply)</li><li>sub mains will consist of steel wire armoured cable mounted on perforated cable tray.</li><li>2 no. new 6 way metal clad distribution boards to be installed.</li><li>4 no. 20A&nbsp;supplies to be installed from new distribution boards to new AC condensers and terminated into IP rated rotary isolators.</li><li>All sub mains and final circuits to be tested and certificates to be issued on completion.</li><li>all circuits and components to be labelled to suit circuit supply reference</li></ul><p><strong>Our total cost to carry out the above works in normal working hours shall be &pound;4,350.75+VAT</strong></p><p>Breakdown</p><p>Labour&nbsp;- &pound;2,600.00</p><p>Materials - &pound;1,675.75</p><p>Certificate&nbsp; - &pound;75.00</p><p>&nbsp;</p><p><strong>PROJECT NOTES:</strong></p><ul><li>It is assumed that all works will be carried out in working hours.</li><li>All isolations will be carried out by others.</li><li>It is assumed parking will be available onsite.</li><li>it is assumed that others will move smoke detectors where required.</li><li>it is assumed any other works not mentioned above will be deemed&nbsp;as extras.</li></ul>