<p>Price for Scaffolding quote ref 1529&nbsp;</p>

<p>To supply erect and dismantle independent tied<br />
scaffold tower and handrail at the above address to<br />
to access gully for clean out and repairs<br />
All working platform will be double boarded with<br />
plastic sheeting between the scaffold boards<br />
double handrails ladder access and toe boards</p>

<p>&pound;1100+vat<br />
Scaffold hire is for 4 weeks hires there after &pound;55</p>

<p>&nbsp;</p>

<p>Price from ASRG&nbsp;</p>

<p>Can&rsquo;t be certain, but the valley gutter appears to be lead, which has been treated with a coating, judging by the crazing it could be one of the single coat repair products, Aquashield or similar, which may not be suited to lead, particular if the correct primer was not applied beforehand.</p>

<p>&nbsp;</p>

<p>This coating repair may well have obscured small splits or defects that are causing the problems.</p>

<p>&nbsp;</p>

<p>Not sure how many leaks are being experienced, but as &nbsp;a first course of action we would suggest:-</p>

<p>&nbsp;</p>

<p><b><u>Specification</u></b></p>

<p>&nbsp;</p>

<p>Two have two roofing operatives attend site for one day.</p>

<p>&nbsp;</p>

<p>Sweep off the worse of the vegetation from the tiled roof slopes either side of the valley, where it is safe to do so (dependant on scaffold handrail)</p>

<p>&nbsp;</p>

<p>(Heavy rain will eventually dislodge this, so it should be cleared otherwise it will wash down and possible block the gutter again)</p>

<p>&nbsp;</p>

<p>We would then clean out the gutter and check that the outlets are clear and free flowing, this may help reduce the amount of ingress.</p>

<p>&nbsp;</p>

<p>(Note: we would rod through with drainage rods, down to ground level, no allowance for specialist, Dynorod or similar)</p>

<p>&nbsp;</p>

<p>Once the gutter is cleaned, we would check the local area above each leak, if nothing is obvious then we may opt to coat an area as a temporary fix</p>

<p>&nbsp;</p>

<p>We would also double check the tiles and mortar pointing, problems with this should be visually apparent, i.e. cracks or splits, which can repair.</p>

<p>&nbsp;</p>

<p><b>Total Cost: &nbsp; &pound; 650.00</b></p>

<p>&nbsp;</p>

<p>When the gutter is clear, we would assess how well adhered the coating is, because it may need to be removed or isolated before a new and suitable coating system is employed, or if a gutter liner system needs to be considered, the tiles either side may require temporary removal to facilitate the new coating or liner, once this has been established we can provide a firm cost for a long term solution.</p>

<p>&nbsp;</p>

<p>We have made no allowance for a skip, we have assumed that the debris being removed are mostly vegetation, so can be spread over a nearby green area or into the client&rsquo;s bin.</p>

<p>&nbsp;</p>

<p>No allowance for scaffolding or access (if Skanska), otherwise we can erect a ladder for access.</p>

<p>&nbsp;</p>

<p>Kind regards,<br />
<br />
Richard Harris&nbsp;<br />
&nbsp;</p>
