<p><strong>East Works</strong></p><p><strong>Construct Compliance Wall</strong></p><ul><li>Construct dividing wall, mesh/cage construction from floor tiles to soffits complete with one secure door</li></ul><p>Total Cost: &nbsp;&pound;8,675.00</p><p><strong>Construct New NOC Wall</strong></p><ul><li>Construct plasterboard wall to seperate&nbsp;NOC including steel mesh in floor void and complete with one secure door</li></ul><p>Total Cost: &nbsp;&pound;14,123.00</p><p><strong>Remove ACU 10</strong></p><ul><li>To decommission and remove unit, strip back electrical supply and pipework including the removal of outdoor condenser</li></ul><p>Total Cost: &nbsp;&pound;12,740.00</p><p><strong>Relocate ACU 15, 16 and 17</strong></p><ul><li>To relocate the units to the position of ACU 10 including the modification of of pipework, new power supply and leak detection</li></ul><p>Total Cost: &nbsp;&pound;25,452.00</p><p><strong>Rotate ACU&#39;s&nbsp;13 and 14</strong></p><ul><li>To de-commission and de-gas pipework, rotate and modify pipework and power supply to suit, extend leak detection and drip tray to suit, re-connect, re-charge pipework and re-commission units</li></ul><p>Total Cost: &nbsp;&pound;14,995.00</p><p><strong>Install New NOC AC Unit</strong></p><ul><li>To install new ACU in current positon of ACU 17 including the modification of existing pipework and power supply, leak detection and drip tray to suit and the installation of new outdoor condenser</li></ul><p>Total Cost: &nbsp;&pound;26,680.00</p><p><strong>Reinstate ACU 9</strong></p><ul><li>To rectify issues raised in validation and re-commission unit</li></ul><p>Total Cost: &nbsp;&pound;8,332.00</p><p><strong>Fresh Air and Extract Air Ventilation</strong></p><ul><li>To use existing fresh air supply, cap off open duct, route ductwork to serve NOC and&nbsp;install fire damper</li></ul><p>Total Cost: &nbsp;&pound;5,871.00</p><p><strong>Rewire Commando Sockets</strong></p><ul><li>To strip back and re-wire sockets in&nbsp;NOC from PDU13&nbsp;and strip back and re-wire sockets outside NOC to&nbsp;PDU9 and PDU10</li></ul><p>?Total Cost: &nbsp;&pound;2,747.00</p><p><strong>Power Supply for ACU&#39;s</strong></p><ul><li>To install new power supply for relocated ACU&#39;s 15, 16 and 17 and install new power supply for new NOC ACU</li></ul><p>Total Cost: &nbsp;&pound;7,696.00</p><p><strong>Power Supply for Security Doors</strong></p><ul><li>To install new power supply for all new doors including fused spurs</li></ul><p>Total Cost: &nbsp;&pound;1,235.00</p><p><strong>Wall Mounted Sockets for NOC</strong></p><ul><li>To install surface mounted single gang 13a outlet with integrated RCD protection rated 30mA fed via radial circuit</li></ul><p>Total Cost: &nbsp;&pound;1,945.00</p><p><strong>Desk Power for NOC</strong></p><ul><li>To install two new under-floor busbars and desk level small power distribution for seven desks</li></ul><p>Total Cost: &nbsp;&pound;5,084.00</p><p><strong>Lighting for NOC</strong></p><ul><li>To strip out existing lighting and replace with LED luminaires and install PIR&#39;s</li></ul><p>Total Cost: &nbsp;&pound;11,287.00</p><p><strong>Containment and Power Supplies for CCTV</strong></p><ul><li>To install new hot dipped galvanised containment for the CCTV systems and install new power supplies for the CCTV panels</li></ul><p>Total Cost: &nbsp;&pound;5,725.00</p><p><strong>Modify Fire Detection for ACU&#39;s</strong></p><ul><li>To modify smoke detection pipework where ACU&#39;s have been removed and install new smoke detection pipework as necessary for new ACU</li></ul><p>Total Cost: &nbsp;&pound;6,790.00</p><p><strong>Relocate HSSD&nbsp;Panel 11</strong></p><ul><li>To&nbsp;isolate panel from fire alarm system and relocate to avoid new desk system</li></ul><p>Total Cost: &nbsp;&pound;1,521.00</p><p><strong>Public Health Services</strong></p><ul><li>To modify existing sprinkler pipework and head positions and install two new branches to suit NOC area</li></ul><p>Total Cost: &nbsp;&pound;3,990.00</p><p><strong>South West Works</strong></p><p><strong>New E Discovery Compliance Wall</strong></p><ul><li>To construct dividing wall in a mesh/cage construction from floor tiles to soffit</li></ul><p>Total Cost: &nbsp;&pound;11,910.00</p><p><strong>Reinstate ACU 2 and 3</strong></p><ul><li>To rectify issues raised in validation and re-commission units</li></ul><p>Total Cost: &nbsp;&pound;18,862.00</p><p><strong>Under Floor Power</strong></p><ul><li>To use existing power supply&nbsp;from PDU 1 and 2 to install under floor power</li></ul><p>Total Cost: &nbsp;&pound;2,301.90</p><p><strong>Lighting</strong></p><ul><li>To install lighting using the existing MER lighting installation</li></ul><p>Total Cost: &nbsp;&pound;2,301.90</p><p><strong>Sprinkler Drain</strong></p><ul><li>To divert sprinkler test&nbsp;drains to avoid new wall</li></ul><p>Total Cost: &nbsp;&pound;2,341.00</p><p><strong>Drawings</strong></p><p>Total Cost: &nbsp;&pound;1,500.00</p><p><strong>Site Protection</strong></p><p>Total Cost: &nbsp;&pound;1,545.00</p><p><strong>O&amp;M Manuals</strong></p><p>Total Cost: &nbsp;&pound;650.00&nbsp;</p><p>Our total cost to carry out the above works in / out of normal working hours shall be</p>