<p>Further to site survey the existing flue system serves 4no Remeha boilers. The flue has been installed using the incorrect fittings and at the incorrect level so the condensation that builds up within the flue cannot escape. This has meant that the flue has now rusted through in several places and has been commended by the gas engineer when he attended site last year. The existing low level flue boiler room needs to be removed and replaced with new. We could not inspect the existing flue that rises up to the roof as it is installed within an old chimney and we did not have the correct access equipment or inspection equipment. We would assume that this section can be re-used as it is vertical section so any condensation that forms within should fall to low level. We assume that the boilers are functional, but have not had the chance to carry out a performance test due to the defective flue.&nbsp;</p><ul><li>Operatives to apply protective sheeting to work routes and working areas.</li><li>To isolate and lock off the 4no Remeha boilers.&nbsp;</li><li>To strip out dispose of the flue located within the boiler room.&nbsp;</li><li>To supply &amp; install the new flue system ensuring hat the correct levels.&nbsp;</li><li>Gas engineer to inspect the works and issue certificate.&nbsp;&nbsp;</li><li>Site to be left clean and tidy.</li></ul><p>Our total cost to carry out the above works in / out of normal working hours shall be &pound;6,317.40</p><p>Breakdown:</p><p>Labour: &pound;1,163.60&nbsp;(2 operatives x 2 days)</p><p>Materials: &pound;4,553.80</p><p>Access Equipment: &pound;250.00</p><p>Certification: &pound;100.00</p><p>Waste: &pound;250.00</p>