<p><strong>Attended site on 23/10/18</strong></p><ul><li>Attended site to investigate issue with lighting in foyer.</li><li>Upon attendance we located a commando plug that had suffered water ingress and the conductors had completely corroded.</li><li>Upon attendance cut back the cores and installed a new plug to rectify the fault.</li><li>Left lighting in correct, working order.</li><li>Site to be left clean and tidy.</li></ul><p>Our total cost to carry out the above works in&nbsp;normal working hours shall be</p><p>Materials - &pound;33.00</p><p>Labour - &pound;168.00</p>