<p>Electrician to re-terminate cable in isolator-laundry</p>

<p>Electrician to rectify phase rotation-laundry</p>

<p>Electrician to rewire high level sockets-corridors</p>

<p>Electrician to replace fan - assisted shower</p>

<p>Electrician to rewire double socket-plant room</p>

<p>Electrician to install junction box-plant room</p>

<p>Electrician to replace outside socket</p>

<p>Electrician to rewire socket-office ground floor</p>

<p>Electrician to rewire socket-office 1<sup>st</sup> floor</p>

<p>Electrician to replace light &ndash; clinical room</p>

<p>Electrician to replace extract isolator-kitchen</p>

<p>Electrician to install switched spur for fan-kitchen</p>

<p>Electrician to install support hanging socket-kitchen</p>

<p>Electrician to replace 5 faulty bulkhead lights in various rooms</p>

<p>Electrician to remove sockets fed from emergency lights above corridor doors</p>

<p>Electrician to install 29 6amp RCBO&rsquo;s for rooms with showers</p>

<p>Electrician to install 3 32amp RCBO for sockets in kitchen</p>

<p>Electrician to install 2 20amp RCBO&rsquo;s for sockets in kitchen</p>

<p>Electrician to install RCD sockets to plant room</p>

<p>Electrician to replace 410 double sockets</p>

<p>Electrician to rewire 3phase washing machine</p>

<p>&nbsp;</p>

<p><span style="font-size:16px;"><b>Items for further investigation</b></span></p>

<p>A cost has been included for the investigation. There could be extra costs to rectify faults after discovering the issues.</p>

<p>DB1 9L1 no earth continuity</p>

<p>DB3 8L3 no earth continuity</p>

<p>DB5 6L1 no earth continuity</p>

<p>DB1 8L2 High earth continuity value</p>

<p>DB3 High earth continuity value on all ring circuits</p>

<p>DB4 High earth continuity value on all ring circuits</p>

<p>DB6 High earth continuity value on all ring circuits</p>

<p>DB3 9L1 High&nbsp;neutral value</p>

<p>DB1 10L3 circuit not found</p>

<p>DB kitchen 10L1 circuit not found</p>

<p>DB Laundry 7L1 circuit not found</p>

<p>DB4 4L1 Circuit not found</p>

<p>1<sup>st</sup> floor sluice socket not working</p>

<p>DB light circuit 2 &amp; 3 very low insulation resistance readings</p>

<p>&nbsp;</p>

<p><span style="font-size:16px;"><b>Works that need confirmation</b></span> (no cost submitted)</p>

<p>Damaged bollards &ndash; unable to source like for like, possible replacement of all bollards?</p>

<p>Replace all corridor ceiling lights &ndash; Greensleeves to confirm lighting style&nbsp;</p>

<p>Install appropriate size MCCB for car charger. The MCCB&rsquo;s are now discontinued so we will have to source a second hand one. The costs vary and the correct size may not be available. A survey should be carried out to find the best solution to power the charger.</p>

<p>New NICEIC certification</p>

<p>&nbsp;</p>

<p>&nbsp;</p>
