<p>The scope of works for this job will be.</p><p>&nbsp;</p><p>&bull;Sign in to site/fill out a T card.</p><p>&bull;Read and sign RAMS.</p><p>&bull;Lay protection around work area where needed.</p><p>&bull;Using steps remove ceiling tiles along the route of containment.</p><p>&bull;Install containment between where the distribution board is located and the A/C isolator.</p><p>&bull;install an adaptable box over where the cable comes through the wall.</p><p>&bull;install 2.5mm fp200 between adaptable box and the DB.</p><p>&bull;replace floating incorrectly installed spur with a wall mounted metal clad spur.</p><p>&bull;isolate the distribution board.</p><p>&bull;terminate the FP200 into the DB using a C20 RCBO.</p><p>&bull;Test the circuit.</p><p>&bull;Reenergise the distribution board.</p><p>&nbsp;</p><p>&nbsp;</p><p>The materials for this job will be:</p><p>&nbsp;</p><p>25m of 2.5mm FP200.</p><p>100x 100mm cable ties. (Metal)</p><p>1x 4x4 adaptable box.</p><p>4x 20mm fire rated stuffing glands</p><p>1x metal clad FSU.</p><p>1x c20 Schneider RCBO</p><p>50x red plugs with screws</p><p>150x m6 penny washers.</p><p>12m of 2&quot; tray.</p><p>8tread steps</p><p>&nbsp;</p><p>This job will take 1-2 men 1 day if steps have to be footed 2 men will have to be prevent.</p><p>&nbsp;</p><p>&nbsp;</p><p>&nbsp;</p>