<ul>
	<li>Emergency out of hours call to attend Pharmacy Walk in Fridge</li>
</ul>

<p>Chiller found to have tripped on HP, adjusting flow valve and reset system.</p>

<p>Found controller to need replacing, return visit carried out the following day and controller fitted.</p>

<p>Tested and left unit running as designed.</p>
