<p>For this job the following will be required.</p><p>&nbsp;</p><p>3x C16</p><p>30m 2.5mm LSF cable.</p><p>&nbsp;</p><p>When investigating the issue, A fault was found on the live conductor between the distribution board and the first point, this cable will need to be replaced using existing containment and also the same cable type (2.5mm LSF).</p><p>Access is bad but manageable.</p><p>Also it was noticed that 3x C16 hager RCBO&#39;s are badly damaged and will require immediate replacement.</p><p>This job will require out of hours working and&nbsp; estimated to take 2 operatives one night.</p><p>&nbsp;</p><p>Access equipment required:</p><p>2x sets of 8 tread steps.</p><p>For this job the following will be required.</p><p>&nbsp;</p><p>3x C16</p><p>30m 2.5mm LSF cable.</p><p>&nbsp;</p><p>When investigating the issue, A fault was found on the live conductor between the distribution board and the first point, this cable will need to be replaced using existing containment and also the same cable type (2.5mm LSF).</p><p>Access is bad but manageable.</p><p>Also it was noticed that 3x C16 hager RCBO&#39;s are badly damaged and will require immediate replacement.</p><p>This job will require out of hours working and&nbsp; estimated to take 2 operatives one night.</p><p>&nbsp;</p><p>Access equipment required:</p><p>2x sets of 8 tread steps.</p>