<ul><li>Air conditioning engineer attended site on 7th June to investigate water leak on AC unit. &nbsp;</li><li>Please note this unit was not installed, nor worked on by the air conditioning company working on behalf of GDC.</li><li>On&nbsp;attendance engineer discovered issue was related to poor gravity fall on core hole to condenser plant, best practice solution is to install in-line condensate pump for which a quote has been sent, see quote Q5594.&nbsp;</li></ul><p>Our total cost to carry out the above works in normal working hours shall be</p>