<p><strong>Attended site on 2/11/18</strong></p><ul><li>Attended site to investigate issue with leak in toilet.</li><li>Upon attendance discovered blocked urinal which caused a flood every time flushed.</li><li>Removed taps and cleaned out.</li><li>Replaced, run and tested.</li><li>Left toilet in correct, working order.</li><li>Site to be left clean and tidy.</li></ul><p>Our total cost to carry out the above works in&nbsp;normal working hours shall be</p><p>&nbsp;</p>