<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>To carry out the modification, engineering, installation and commissioning of the existing control system encompassing a motor panel manufactured to cupboard styles construction.&nbsp;</li>
	<li>To control panel will incorporate the following, 1no&nbsp;door interlocked isolator, 1no panel live LED, 1no fire circuit healthy/fail LED.</li>
	<li>Manual motor starters, with Hand/off/Auto switches, auto changeover will be carried out by the pump enabled/fault LEDs for 1no CT heating pump (Twin head) - 1ph/4kw max, 1no VT Heating pump (twin head) 1ph/4kw max, 1no HWS primary Pump (Twin Head) 1ph/4kw Max, 1no HWS secondary pump (single) 1ph/2kw Max.&nbsp;</li>
	<li>Hand/off/auto switches, enabled/ fault LED&#39;s for 1no heating boiler - 2kw max.</li>
	<li>Additional indication LED&#39;s and switches for 1no summer/winter selector switch suitable rated and protected power supplies for: 1no. RCD 13amp double socket 1 in N. Immersion heater - 3kwW Max 1 in no control circuit.&nbsp;</li>
	<li>Interface relays, fault relays, transformers, Traffolyte&nbsp;labels. The control panel will be provided with bottom entry glands and outgoing terminals. White labels with black lettering will be located on the fascia of the control panel for all switches and LEDs to be identified. Internal items such as relays and contractors will be identified in line with the control panel wiring diagram. The external and internal Schneider panel finish will be grey RAL7035 powder structure paint. The internal chassis plate will be galvanised zinc-plated. All cables will be boot lace Ferrell connected.&nbsp;</li>
	<li>To supply &amp; install the new control panel within the plant room, we assume suitable wall space and power supply will be made available. To provide electrical services to plant listed above emanating fro the control panel.&nbsp;</li>
	<li>To supply &amp; install new mechanical plant power wiring and containment to the items listed.&nbsp;</li>
	<li>To supply &amp; install an external sensor on the nearest suitable north facing wall. Final sensor position to be mutually agreed.&nbsp;</li>
	<li>Any fire alarm interface unit is to be mounted next to the MCP to terminate into.&nbsp;</li>
	<li>Site to be left clean and tidy.</li>
</ul>

<p>Project Note: We assume all the required pump speed invertors and pressure transducers will be integral to all pump units where required. We have not allowed to supply or install separate speed invertors or transducers for any plant equipment. We assume any boiler shunt pumps will be directly electrically connected to an controlled by its associated boiler. No allowance has been made to incorporate these into the control panel. We have made no allowance to supply or install any meters. We have made no allowance to supply or install any fire alarm interface unit. Any additional works required will be of additional cost. Any lighting, small power or any works other than listed above,&nbsp;Remote pressure transducers for the pumps,&nbsp;Damper motors, any mewps, scaffolding or access towers, Gas detection systems or solenoids or water solenoids not listed in equipment section, any works involving fire dampers, PC headend and graphics, any level switches for the tanks, any solenoid valves, three or two port valves with actuators not listed in the equipment schedule, any energy meters, any ductwork or grilles of any kind (A/C ductwork included), differential pressure switches for the fans or pumps, Any Co2 detectors other than the two listed in the equipment section, Any network points to be provided by others, Any valve insulation bags for the three port or two port valves, Any inverter speed drives, Any strip out/removal of existing equipment, Any thermostats or protective covers for the thermostats or sensors, Any other work or equipment not specifically listed above.&nbsp;</p>
