<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>Replace distrubution boards DB A, DB B &amp; DB C to introduce RCD protection and to tidy up non compliant cabling terminations</li>
	<li>Replace rotary isolator in kitchen</li>
	<li>Replace water equipotential earth bonding clamp</li>
	<li>Replace socket in dining room</li>
	<li>Install protection to cable in corridor by reception</li>
	<li>Install black PVC conduit to outside light cable</li>
	<li>Replace socket in maintenance shed</li>
	<li>Replace socket in TV room</li>
	<li>Identify neutral conductor in DB maintenance</li>
	<li>Install cable clips on outside cable</li>
	<li>Install protection for single insulated cables in loft</li>
	<li>Replace 5no bulkhead lights in various locations</li>
	<li>Replace 4&quot; fan</li>
	<li>DB 5B replace distribution board</li>
</ul>

<p><strong>Items for futher investigation (</strong>a cost has been included for the investigation of the below items, an uplift maybe required to rectify faults after discovering the issues).</p>

<ul>
	<li>Laundry DB 2.5mm cable terminated in main switch</li>
	<li>Laundry DB red cables terminated in earth bar</li>
	<li>DB 5 2.5mm cable terminated in main switch</li>
	<li>DB ccu 1 unknown circuits</li>
	<li>DB 5A two cables in main switch and 100MA RCD</li>
	<li>Cable run in duct laying on ground</li>
</ul>

<p>There are other circuits in need of RCD protection, these will need to be surveyed to establish if new distribution boards are needed or if replacement RCBO&#39;s can be sourced.</p>

<ul>
	<li>New NICEIC certification</li>
	<li>Site to be left clean and tidy.</li>
</ul>
