<p class="Default"><b>Please find as follows the scope of works and our costings based on these works,</b></p>

<p class="Default"><b>Level 2 </b></p>

<p class="Default"><b>AHU&rsquo;s 20 &amp; 21 plant 15 </b></p>

<p class="Default">- Remove and replace existing with new relays, terminals, &nbsp;fixings and contactors, door panel lamps to power section panel equipment</p>

<p class="Default">- supply and install new Inverters to AHU</p>

<p class="Default">- DB to be installed adjacent to the panel to enable AHU fans to operate during upgrade works</p>

<p class="Default">- Re wire &nbsp;the &nbsp;4 no. existing inverters</p>

<p class="Default"><b>Plant 6 Panel 14 </b></p>

<p class="Default">- Remove and replace existing with new relays, terminals, &nbsp;fixings and contactors, door panel lamps to power section panel equipment</p>

<p class="Default">-install &nbsp;3 phase 200A distribution board to the rear of the control panel.</p>

<p class="Default">- Install &nbsp;30kW inverter and 18.5KW &nbsp;to same location.</p>

<p class="Default">- Install &nbsp;new wiring for all fans &nbsp;from the control panel and inverter. &nbsp;The existing wiring installation is not to a satisfactory level and they and are not to the standard for field wiring from a frequency inverter.</p>

<p class="Default">- Install local isolators for fans (4 pole)</p>

<p class="Default">- Remove faulty inverters and dispose.</p>

<p class="Default">&nbsp;-On completion remove all redundant parts, wiring and equipment and make good to all panels, housings and tray work. &nbsp;</p>

<p class="Default">- Supply and issue new control panel diagrams</p>
