<p>as requested by Colin hale we have allowed for 1 no.&nbsp;electrician to be in attendance to guide and assist Carillion&nbsp;staff pulling in the armoured cable and installing cable tray.&nbsp;</p><p>the below costs allow for 1 no. electrician for 5 no. shifts,&nbsp;if more than 5 no. shifts are required due to delays with cable pull and tray installation then these will be additional costs.</p><p>cable to be tested before we leave site ( to be witnessed by carillion) if found to be faulty on return this will be an additional costs to replace.</p><p>electrician to check standards of work are acceptable before signing off.</p><p>electrician to attend to carry out final connections and testing ( electrician will need a carillion member of staff present as he can not work alone in the HV switch room)</p><p><strong>Documentation / Specifications</strong></p><p>This quotation has been compiled based on the following documentation / specifications:</p><p>Dwg&nbsp;160033-EQ&nbsp;Electrical Installation</p><p><strong>Scope of Works</strong></p><p>We have allowed for the following scope of works associated with the new cabin supply:</p><p>1. Power Cabling + Rotary Isolator +MCCB</p><p>2. Cable Management</p><p>3. Cable Testing</p><p><strong>1) Power Cabling</strong></p><p>We have allowed for the supply, installation and termination of the site run low voltage power cabling. We have allowed for the below cabling:</p><p>from: Existing&nbsp;MCCB&nbsp;Board located within HV Container</p><p><strong>to: New cabin main DB</strong></p><p><strong>Cable type: SWA</strong></p><p><strong>Size:&nbsp;50mm</strong></p><p><strong>Cores: 5&nbsp;</strong></p><p><strong>Cable length:&nbsp;230M</strong></p><p>We have allowed for the supply and installation of a Rotary Isolator adjacent the Main Cabin DB.</p><p>We have allowed for the supply and installation of a New&nbsp;100A&nbsp;Schneider&nbsp;MCCB</p><p>&nbsp;</p><p>2)&nbsp;<strong>Cable Management</strong></p><p>We have allowed for the supply and installation of&nbsp;140m&nbsp;Medium Duty tray to support the supplied cable for its length when not installed in duct</p><p>Note: We have assumed that the rest of the cable will be run in ducts that are supplied and</p><p>installed by others. (Approx. 85m in duct)</p><p>We have assumed that ducts will be free of debris and have sufficient capacity for our cables</p><p>3)&nbsp;<strong>Cable Testing</strong></p><p>We have allowed for the completion of all cable testing associated with the items being supplied or installed by us.</p><p>We have allowed for the generation of all test certificates, completion of all tests and the provision of any necessary test equipment.</p><p><strong>Exclusions from Scope of Supply</strong></p><p>The following items are specifically excluded from our scope of supply:</p><p>Civil works other than minor holes for cable penetrations</p><p>Temporary Works</p><p>Removal of redundant Cabling/Equipment</p><p>Commissioning</p><p>Any Cabling from the New Cabin Main DB to the outgoing circuits</p><p><strong>Assumptions</strong></p><p>We have assumed that we will have good unhindered access to the site for delivery and installation of all equipment.</p><p>It is assumed the work will be carried out during a normal working week (Monday &ndash; Friday 07:00hrs&nbsp;- 17:00hrs) If weekend work and/or out of hours&rsquo; work is required this will be charged at additional cost</p><p>We have assumed that there is sufficient spare capacity for installation of a new&nbsp;MCCB&nbsp;in the HV Container&nbsp;MCCB&nbsp;Board</p><p>We have assumed there is sufficient spare capacity to feed the new cabin from the&nbsp;MCCB&nbsp;board in the HV container</p><p><strong>Standards, Regulations and Requirements</strong></p><p>We will comply with the latest editions of the following standards, codes of practice and regulations:</p><p>International Electrical Code (IEC) Standards</p><p>The IEE Wiring Regulations for Electrical Installations</p><p>COSHH&nbsp;Regulations</p><p>Electricity at Work Regulations</p><p>Health &amp; Safety at Work Order</p><p>WEEE&nbsp;&ndash; Waste Electrical and Electronic Equipment Directive</p><p>&nbsp;</p><p><strong>Our total cost to carry out the above works in&nbsp;normal working hours shall be &pound;6,524.41</strong></p><p><strong>BREAKDOWN</strong></p><p><strong>Labour - &pound;1,400.00+VAT</strong></p><p><strong>Materials - &pound;5,049.41+VAT</strong></p><p><strong>test certificate - &pound;75.00+VAT</strong></p>