<p><strong>option A - use existing cctv supply (circuit supply reference not known)</strong></p><p>we have assumed that the existing circuit is installed to current regulations and no costs have been allowed to modify the circuit other than the below scope of works.</p><ul><li>operative to attend site and sign in.</li><li>work area to have protection and barriers installed as required</li><li>1 no. scaffold tower to be erected by PASMA trained operative</li><li>circuit reference to existing cctv&nbsp;supply to be ascertained.</li><li>new containment to be installed from existing cctv&nbsp;containment tray to new door opener location ( involves galvanised conduit supplying 1 no. switched fused spur and 1 no. single gang box for a card reader)</li><li>wiring to be installed and all components second fixed</li><li>existing circuit to be isolated by deutsche bank engineer ( to carry out full testing we will need access to the distribution board)</li><li>new swa cable to be connected to existing cctv supply using the existing connection box</li><li>full testing to be carried to modified circuit and all results recorded</li><li>minor works certificate to be issued on completion.</li></ul><p><strong>our total cost to carry out the above works out of hours shall be &pound;1,101.00+VAT</strong></p><p><strong>Labour&nbsp;- &pound;676.00+VAT</strong></p><p><strong>Materials - &pound;175.00+VAT</strong></p><p><strong>Access equipment - &pound;150.00+VAT</strong></p><p><strong>Certificate - &pound;100.00+VAT</strong></p><p><strong>option B&nbsp;- Install new circuit to feed electric door closer using existing containment</strong></p><p>it is assumed that the existing distribution board has a spare away.<strong>&nbsp;</strong></p><ul><li>operative to attend site and sign in.</li><li>work area to have protection and barriers installed as required</li><li>1 no. scaffold tower to be erected by&nbsp;PASMA&nbsp;trained operative</li><li>new containment to be installed from existing&nbsp;cctv&nbsp;containment tray to new door opener location ( involves&nbsp;galvanised&nbsp;conduit supplying 1 no. switched fused spur and 1 no. single gang box for a card reader)</li><li>wiring to be installed and&nbsp;all components second fixed</li><li>new 4MM 3 CORE&nbsp;Steel wire aarmoured cable to be installed from the distribution board cupboard to the new door closer location using the existing containment for the cctv&nbsp;</li><li>new swa cable to be connected to newly installed spur</li><li>any penetrations that are made in the building fabric are to be sealed using intumesent mastic</li><li>full testing to be carried to modified circuit and all results recorded</li><li>minor works certificate to be issued on completion.</li></ul><p><strong>our total cost to carry out the above works out of hours shall be &pound;1,351.00+VAT</strong></p><p><strong>Labour&nbsp;- &pound;676.00+VAT</strong></p><p><strong>Materials - &pound;425.00+VAT</strong></p><p><strong>Access equipment - &pound;150.00+VAT</strong></p><p><strong>Certificate - &pound;100.00+VAT</strong></p>