<ul>
	<li>Operative attended site 09/02/2020.</li>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>Upon attendance discovered some lights after the power cut had not come back on and need to be rectified.</li>
	<li>To remove existing damaged ballast.</li>
	<li>To supply and install new ballast.</li>
	<li>To supply and instl new&nbsp;Passive infrared sensor.</li>
	<li>To test and inspect in correct working order.</li>
	<li>Site to be left clean and tidy.</li>
</ul>
