<p>Whilst on site various issues were found:</p><p>&nbsp;</p><p><strong>Quote one:</strong></p><p>Urgent work required:</p><ul><li>A Remeha Gas 210 eco pro service engineer (showing E14) both boilers are showing this.</li><li>Various leaks on expansion joints for the pumps as you walk in they&rsquo;re on the left. (I have tried tightening to no avail these have started to rust due to this problem being undetected for a long period of time. These will need to be removed, cleaned and resealed at a minimum or possibly replacing but this will be down to the engineer to decide once removed.</li><li>Gas safe engineer to check why there are lock off tags in place and to check that the system is safe to continue/begin operating remove tags once this has been confirmed.</li><li>Engineer to check the heating system pressurisation unit as this is showing two codes (SER AND HPR)</li><li>The system will also need an engineer to fix the fault with the Gas booster.</li><li>A BMS engineer to check fault codes on the system and to fix and clear the log once complete.</li></ul><p><strong>Quote two:</strong></p><p>Other than the immediate repair work needed it is highly recommended that:</p><p>All equipment in the plant room is serviced to prevent further issues arising. When the engineer is on site carrying out the repair work he will be able to assist with listing all serviceable equipment in the room and how long this will take.</p><p>&nbsp;</p><p><strong>Quote three?</strong></p><p>&nbsp;Periodic preventative maintenance / servicing needs to be put in place for the complete plant.</p><p>&nbsp;</p>