<p>The below costs are priced&nbsp;on the assumption that the work areas are free of Asbestos&nbsp;(no costs have been allowed for a&nbsp;survey or to carry out removals)</p><p>it is assumed that parking is available on site.</p><p>it is assumed that a skip can be left on site.</p><p>it is assumed that we will have free access to all work areas.</p><p><strong>Electrical:</strong></p><p>Electrical strip out</p><p>Fire Alarm</p><ul><li>Isolate, disconnect and remove existing&nbsp;Tasfire&nbsp;fire alarm panel and all associated wiring and accessories</li><li>Retain existing OOW fire alarm interface link for future use.</li></ul><p>Electrical Installation:</p><ul><li>Isolate, disconnect and remove all final circuit from&nbsp;MDBA&nbsp;(Navy News distribution board) including all wiring and containment.</li><li>Isolate disconnect and remove&nbsp;MDBA&nbsp;and sub main SWA wiring back to source.</li><li>Disconnect and remove redundant PA speakers.</li><li>Remove and dispose of all wiring accessories, containment, luminaries and electrical equipment</li><li>Small power installation to meet following requirements (all wiring accessories to be surface mounted)</li></ul><p><strong>Switchgear &amp; Distribution:</strong></p><ul><li>Supply and install new panel board to plant room.</li><li>Terminate new supply cable into panel board (new supply provided by others)</li><li>Install following sub main supply circuits to new panel board:</li></ul><p>&nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp;1.&nbsp;Flat 1 CU</p><p>&nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp;2.&nbsp;Flat 2 CU</p><p>&nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp;3.&nbsp;Flat 3 CU</p><p>&nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp;4.&nbsp;Plant room DB</p><p>&nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp;5.&nbsp;Fire Alarm (final circuit)<strong>&nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp;</strong></p><p><strong>Lighting Works</strong></p><p><strong>Flat 1</strong></p><ul><li>Supply and install consumer unit to suitable location within Flat and connect to Flat 1 sub main.</li><li>Lighting installation to meet following requirements (Switching arrangements to be agreed with Project Manager); All wiring accessories to be flush mounted.</li></ul><p><strong>Kitchen Area</strong></p><p>&nbsp; &nbsp; &nbsp;3No. down lights (Inc. 1no. Integral emergency unit)</p><p><strong>&nbsp; &nbsp; &nbsp;Dining Area</strong></p><p>&nbsp; &nbsp; &nbsp;4No. down lights (Inc. 1no. Integral emergency unit)</p><p>&nbsp; &nbsp; &nbsp;2No. wall lights</p><p><strong>&nbsp; &nbsp; &nbsp;Lounge Area</strong></p><p>&nbsp; &nbsp; &nbsp;4No. down lights (Inc. 1no. Integral emergency unit)</p><p>&nbsp; &nbsp; &nbsp;2No. wall lights</p><p><strong>&nbsp; &nbsp; &nbsp;Bedroom 1</strong></p><p>&nbsp; &nbsp; &nbsp;6no. down lights (Inc. 1no. Integral emergency unit)</p><p>&nbsp; &nbsp; &nbsp;2No. reading lights</p><p><strong>&nbsp; &nbsp; &nbsp;Bedroom 2</strong></p><p>&nbsp; &nbsp; &nbsp;2No.down lights (Inc. 1no. Integral emergency unit)</p><p>&nbsp; &nbsp; &nbsp;1No. reading</p><p><strong>&nbsp; &nbsp; &nbsp;Toilet</strong></p><p>&nbsp; &nbsp; &nbsp;3No. down lights (Inc. 1no. Integral emergency unit)</p><p>&nbsp; &nbsp; &nbsp;1No. Extract Fan</p><p><strong>&nbsp; &nbsp; &nbsp;Bathroom</strong></p><p>&nbsp; &nbsp; &nbsp;3No. down lights<strong>&nbsp;</strong>(Inc. 1no. Integral emergency unit)</p><p>&nbsp; &nbsp; &nbsp;1No.&nbsp;backlit&nbsp;mirror c/w shaver point</p><p>&nbsp; &nbsp; &nbsp;1No. Extract Fan</p><p><strong>&nbsp; &nbsp; &nbsp;</strong></p><p><strong>Entrance Hallway</strong></p><p>3No. down lights<strong>&nbsp;</strong>(Inc. 1no. Integral emergency unit)</p><p><strong>External</strong></p><p>1No. outside light</p><p>Small power installation to meet following requirements (all wiring accessories to be flush mounted)</p><p><strong>Kitchen</strong></p><p>3No. twin socket outlets</p><p>3No. fused connection units (and load side socket outlets where required) for appliances</p><p><strong>Dining Area</strong></p><p>2No. twin socket outlets</p><p><strong>Lounge Area</strong></p><p>3No. twin socket outlets</p><p><strong>Bedroom 1</strong></p><p>3No. twin socket outlets</p><p><strong>Bedroom 2</strong></p><p>2No. twin socket outlet</p><p><strong>Entrance Hallway</strong></p><p>1 No. twin socket outlet</p><p>Install aerial point to television location and connect to main aerial installation.<strong>&nbsp;</strong></p><p><strong>Flat 2</strong></p><ul><li>Supply and install consumer unit to suitable location within Flat and connect to Flat 2 sub main.&nbsp;</li><li>Lighting Installation to meet following requirements (switching arrangement to be agreed with Project Manager) : (all wiring accessories to be flush mounted)</li></ul><p><strong>&nbsp;</strong></p><p><strong>Kitchen/Dining Area</strong></p><p>4No. down lights (Inc. 1No Integral emergency unit)</p><p><strong>Lounge Area</strong></p><p>8No. down lights (Inc. 1No Integral emergency unit)</p><p>4No. wall lights</p><p><strong>Bedroom 1</strong></p><p>4No. down lights (Inc. 1No Integral emergency unit)</p><p>2No. reading lights</p><p><strong>Bedroom 2</strong></p><p>2No. down lights (Inc. 1No Integral emergency unit)</p><p>1No. reading light</p><p><strong>Bathroom / Toilet</strong></p><p>3No. down lights (Inc. 1No Integral emergency unit)</p><p>1No.&nbsp;backlit&nbsp;mirror c/w shaver point</p><p>1No. Extract fan</p><p><strong>Entrance Hallway</strong></p><p>3No. down lights (Inc. 1No Integral emergency unit)</p><p><strong>Storage Cupboard</strong></p><p>2No. down lights</p><p><strong>External</strong></p><p>1No. Outside Light</p><p>Small power installation to meet following requirements (all wiring accessories to be flush mounted)</p><p><strong>&nbsp;</strong></p><p><strong>&nbsp;</strong></p><p><strong>Flat 3</strong></p><ul><li>Supply and install consumer unit to suitable location within flat and connect to Flat 3 sub main.</li><li>Lighting installation to meet following requirements (switching arrangements to be agreed with project manager: (all wiring accessories to be flush mounted)</li><li>All wiring accessories are to be installed to comply with current DDA Regulations with regard to heights</li></ul><p>&nbsp;Small power installation to meet following requirements (all wiring accessories to be flush mounted)</p><p><strong>&nbsp;Kitchen Area</strong></p><p>&nbsp;4No. down lights (Inc. 1No Integral emergency unit)</p><p><strong>&nbsp;Dining Area</strong></p><p>&nbsp;5No. down lights (Inc. 1No Integral emergency unit)</p><p>&nbsp;2No. wall lights</p><p><strong>&nbsp;Lounge Area&nbsp;</strong></p><p>&nbsp;5No. down lights (Inc. 1No Integral emergency unit)</p><p>&nbsp;2No. wall lights</p><p><strong>&nbsp;Bedroom 1</strong></p><p>&nbsp;4No. down lights (Inc. 1No Integral emergency unit)</p><p>&nbsp;2No. reading lights</p><p><strong>&nbsp;Bedroom 2</strong></p><p>&nbsp;6No. down lights (Inc. 1No Integral emergency unit)</p><p>&nbsp;1No. reading light</p><p><strong>&nbsp;Toilet</strong></p><p>&nbsp;2No. down lights (Inc. 1No Integral emergency unit)</p><p>&nbsp;1No. Extract Fan</p><p><strong>&nbsp;Shower Room</strong></p><p>&nbsp; 2No. down lights (Inc. 1No Integral emergency unit)</p><p>&nbsp; 1No.&nbsp;Backlit&nbsp;mirror c/w shaver point</p><p>&nbsp; 1No. Extract Fan</p><p><strong>&nbsp; Entrance Hallway</strong></p><p>&nbsp; 2No. down lights (Inc. 1No Integral emergency unit)</p><p><strong>&nbsp; Storage Cupboard</strong></p><p>&nbsp; 2No. down light</p><p>&nbsp;&nbsp;<strong>External</strong></p><p>&nbsp; 1No. Outside Light</p><p><strong>&nbsp; Kitchen</strong></p><p>&nbsp; 4No. twin socket outlets</p><p>&nbsp; 3No. fused connection units (and load side socket outlets where required) for appliances</p><p><strong>&nbsp; Dining area</strong></p><p>&nbsp; 1No. twin socket outlet</p><p><strong>&nbsp; Lounge Area</strong></p><p>&nbsp; 3No. twin socket outlets</p><p><strong>&nbsp; Bedroom 1</strong></p><p>&nbsp; 3No. twin socket outlets</p><p><strong>&nbsp; Bedroom 2</strong></p><p>&nbsp; 3No. twin socket outlets</p><p><strong>&nbsp; Entrance Hallway</strong></p><p>&nbsp; 1No. twin socket outlets</p><p>&nbsp; Install aerial point to television location and connect to main aerial installation</p><p><strong>&nbsp;</strong></p><p><strong>Plant Room</strong></p><ul><li>Supply and install distribution board and connect to&nbsp;plantroom&nbsp;sub main.&nbsp;</li><li>Lighting installation to meet following requirements and switching arrangements to be agreed with project manager</li></ul><p>&nbsp; &nbsp; &nbsp; &nbsp; &nbsp; 4no. LED strip lights</p><p>&nbsp; &nbsp; &nbsp; &nbsp; &nbsp; 1no. LED strip light c/w 3 hour integral emergency pack</p><ul><li>Small power installation</li></ul><p>&nbsp; &nbsp; &nbsp; &nbsp; &nbsp; 2no. twin metal clad socket outlets</p><ul><li>Supply and install digital television aerial to roof and associated wiring to 3 way splitter in plant room</li></ul><p><strong>Verification and commissioning</strong></p><ul><li>Provide O&amp;M manual containing containing schedules, test certificates and installation&nbsp;datasheets&nbsp;as required</li></ul><p><strong>&nbsp; &nbsp; &nbsp;</strong></p><p><strong>Total Cost of works: &pound;46,987.14 + VAT</strong></p><p><strong>&nbsp;</strong></p><p><strong>Dreadnought&nbsp;HMNB&nbsp;Portsmouth</strong></p><p><strong>External works</strong></p><p><strong>Ground floor rear entrance DDA ramp</strong></p><ul><li>Uplift paving slabs and excavate pathway for new DDA compliant access ramp.</li><li>Supply and install consolidated hardcore sub-base.</li><li>Form timber shuttering for new concrete DDA ramps</li><li>Lay new concrete tampered finish DDA ramp to rear access door area.</li><li>Install new DDA compliant stainless steel handrail.</li><li>Reinstate paving/tarmac to ramp perimeter.</li><li>On completion strike&nbsp;formwork&nbsp;and leave area in clean &amp; tidy condition.</li></ul><p><strong>External door for server room</strong></p><ul><li>Form new opening in external rear elevation for access to new server room.</li><li>Install new lintel with&nbsp;UPVC&nbsp;external door complete with ironmongery, lock with 3 keys.</li><li>Make good internal &amp; external wall areas.</li></ul><p><strong>DDA Compliant Access door</strong></p><ul><li>Strip out and remove existing door and window to rear facade</li><li>Adapt existing opening for DDA compliant access door.</li><li>Supply and install new&nbsp;UPVC&nbsp;DDA compliant access door with ironmongery and door furniture.</li><li>Make good wall areas and decorate to match existing</li><li>Remove all debris for safe disposal.</li></ul><p><strong>Provisional Sum</strong></p><p><strong>Install new soil external Sub stack for Flat 4</strong></p><ul><li>Install new&nbsp;110mm&nbsp;soil vent pipe to flat for bathroom.</li><li>Excavate path area for trench and install new&nbsp;110mm&nbsp;underground pipe to the correct fall</li><li>Break into existing Manhole and connect new services to main drain run</li><li>Backfill trench with compact layers and make good path area.</li></ul><p><strong>Demolition work and strip out</strong></p><ul><li>Ground and First Floor</li><li>Strip out existing non structural partitions, doors, frames, toilets, sanitary wear and floor coverings as per drawings provided.</li><li>All waste to be segregated and transferred for safe disposal.</li></ul><p><strong>Building works</strong></p><p><strong>Ground floor Flat 1 toilet</strong></p><ul><li>Core hole into external wall for water waste services for toilet area.</li><li>Excavate path area for trench and install new&nbsp;110mm&nbsp;underground pipe to the correct fall.</li><li>Break into existing Manhole and connect new services to main drain run.</li><li>Backfill trench with compact layers and make good path area.</li><li>Erect new stud partition to form new toilet and tape &amp; joint new plasterboard walls.</li><li>Install new DDA complaint access door with ironmongery and door furniture.</li><li>Apply self&nbsp;levelling&nbsp;floor compound to floor area.</li><li>Supply and install&nbsp;Polysafe&nbsp;hydro safety flooring with coved skirting detail.</li><li>Supply new DDA compliant shower cubicle with Fold down seat.</li><li>Install new DDA complaint WC</li><li>Install new Mira shower with adjustable rail.</li><li>Install new wash hand basin and DDA complaint taps.</li><li>Install DDA compliant drop bars/handrails.</li><li>Install mirror.</li><li>Install DDA compliant toilet Accessories pack.</li><li>Supply and install white ceramic wall tiles to toilet area.</li><li>Install manifestation to window area.</li><li>On completion remove all debris and leave work area in clean tidy condition.</li></ul><p><strong>Flat 1</strong></p><ul><li>Install new partition to form Server room.</li><li>Adapt opening and install internal DDA compliant door to hallway</li><li>Supply and install DDA complaint kitchen as per drawing.</li><li>Install new partition wall to form Bedroom 2 and install door to DDA compliant building&nbsp;regs&nbsp;part M</li><li>Install new DDA complaint door to bedroom 1 and fire exit door as per drawing</li></ul><p><strong>Provisional sum</strong></p><p>Structural engineer to attain if walls to be removed are non load bearing</p><p><strong>First floor</strong></p><p><strong>Landing area</strong></p><ul><li>Carry out alterations to existing handrail by removing back section and installing plasterboard partition.</li></ul><p><strong>Flat 2</strong></p><ul><li>Form new opening into existing wall area and install entrance door /frame with door furniture to flat entrance in lobby area.</li><li>Form new opening into existing wall area and install entrance door /frame with door furniture to lounge/diner area.</li><li>Supply and install new doors to Bedrooms 1,2 and 3</li><li>Supply white ceramic wall tiles and non slip floor tiles to bathroom area.</li><li>Install new bath, wash hand basin with mono bloc tap and new WC.</li><li>Install new stud partition to from Bedroom 3</li><li>Supply and install new kitchen as per drawing.</li><li>Install fire exit to lobby area.</li></ul><p><strong>Flat 3</strong></p><ul><li>Form new opening into existing office wall area and install entrance door /frame with door furniture to form bedroom 3&nbsp;</li><li>Supply and install new stud partition to form kitchen and bathroom wall.</li><li>Replace and reverse hang entrance door to flat 3</li><li>Supply and install new door and partition to separate flats.</li></ul><p><strong>Flat 4</strong></p><p>Allowance to install services to flat electric, water (Hot &amp; cold) for future refurbishment of flat)</p><p>Allowance to move door and change swing direction at top of stairs.</p><p><strong>Decoration and finishes</strong></p><p>Apply 1no undercoat, 2 x topcoats emulsion paint to&nbsp;colour&nbsp;scheme approved by the client to existing surfaces or newly boarded surfaces.</p><p>All skirting woodwork and&nbsp;architraves&nbsp;to be decorated white 1 x primer 1x undercoat and 2 x topcoats.</p><p>Manifestation.</p><p>Reflective film applied to all windows associated with DDA flat one and newly formed server room.</p><p>Bathrooms and Wc windows to receive obscure window film.</p><p>Supply canopy and DDA lighting and automated door access opening for the front door.</p><p>&nbsp;</p><p><strong>Total Cost for Works: &pound;159,580.00&nbsp;+ VAT</strong></p><p><strong>Prelims</strong></p><p>Site supervisor for 12 weeks &pound;16,800.00</p><p>Temporary lighting &pound;500.00</p><p>Project manager attendance 1 day per week &pound;4080.00</p><p>O &amp; M Manual &pound;450.00</p><p>Waste management &pound;1000.00</p><p>Access equipment &amp; protection &pound;750.00</p><p><strong>Provisional sum</strong></p><p>&pound;4000.00 for new ceilings</p><p>Existing services to first floor not being removed allowance to box in and paint &pound;2000.00</p>