<p>Plumber attended site on 9th August to fix the following issues:-</p><p><strong>Job 1: Blocked toilet on 1st floor ladies toilet</strong></p><ul><li>Plumber went to look at blocked toilet but this had already been unblocked.</li></ul><p><strong>Job 2: Broken&nbsp;toilet seat on 3rd floor gents toilet</strong></p><ul><li>Removed 1 no. broken toilet seat and replaced with new.</li><li>Removed 2 no. toilet seats and refitted. &nbsp;</li><li>Site to be left clean and tidy.</li></ul><p><strong>Breakdown</strong></p><p>Labour: &pound;178.50</p><p>Materials: &pound;24.20</p><p>Our total cost to carry out the above works in normal working hours shall be</p>