<p><strong>Re: Winchester House &ndash; Replacement of Gas Booster Pumps &amp; Control Panel</strong></p><p>Further to your enquiry regarding the above, please find below our quotation to attend site and carry out the works associated with the replacement gas booster pumps and control panel.</p><p>The works would consist of the following:</p><p>&bull; Carry out an in-depth survey of the existing pumps, controls and associated pipe work prior to works commencing on site.</p><p>&bull; Carry out a gas pressure / soundness test on the existing system. If a leak is evident then this will need to be quoted and repaired before any works commence.</p><p>&bull; Disconnect the existing electrical supplies to the 2 no. pumps and control panel.</p><p>&bull; Disconnect the existing flexible pipe work connect.</p><p>&bull; Unbolt and remove from the existing gas booster pumps and the control panel from their current locations. These redundant items of plant will be removed from site and disposed of in the correct manner.</p><p>&bull; The new gas booster pumps and control panel will then be lifted into position and secured into place.</p><p>&bull; RE-connect the gas pipe work using the new flexible connecting and modify the pipe work if required.</p><p>&bull; Reconnect the power supplies to the pumps and to the control panel.</p><p>&bull; Carry out a gas pressure / soundness test on the new pumps and associated pipe work.</p><p>&bull; Reconnect the existing BMS cabling and ensure that the system controls correctly. Please note that this is optional as the BMS works may be carried out by the in-house operatives. Please also not that we have not allowed for any additional BMS hardware.</p><p>&bull; Test the system and set into operation.</p><p>&bull; Provide O&amp;M information for the completed works.</p><p>&nbsp;</p><p><strong>Our cost to carry out the above works amounts to: &pound;45,219.35+VAT. Please note that this includes the supply of all the Nu-Way equipment and all the labour and materials required to replace the 2 no. as booster pumps and 1 no. control panel.</strong></p><p><strong>The optional cost to carry out the BMS works amounts to &pound;1,529.50 Plus VAT</strong></p><p><strong>PROJECT NOTES</strong></p><ul><li>Please note that all works are to be carried out, out of normal working hours. We would suggest pressure testing the system on a Friday evening. This will allow the main works to commence on the Saturday morning and&nbsp;ensure&nbsp;that all works are complete and ready for testing on the Sunday afternoon.</li><li>Note that we have not allowed for any attendance from the incumbent fire alarm contractor should they be required to attend site and isolate any fire alarms or to disconnect / connect any fire alarm links to the existing or new panel.</li></ul><p>&nbsp;</p><p>&nbsp;</p>