<p><u><strong>Option 1&nbsp;</strong></u></p>

<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>Supply &amp; fit puddle sucker pump with automatic on and off control.&nbsp;</li>
	<li>This&nbsp;will be sited with in the UPS room where the floor has been lifted on the left hand side of the room.&nbsp;</li>
	<li>New electrical supply will be installed fro fuse board located in another room.&nbsp;</li>
	<li>Supply approximately 20m of FP200 cabling, fixture and fittings this will be installed above ceiling area, dropping into UPS room to supply a 13amp fused spur near to sump pump.&nbsp;</li>
	<li>NICEIC electrical insulation certificate will be provided for works carried out.&nbsp;</li>
	<li>450MM x 450mm fire rated access panels will need to be cut out to gain access above boarded ceilings where required, 1no access hatch has been allowed for.&nbsp;</li>
	<li>Pumped water will rise up approx 5-6m and full to nearest waste point (pipework size 1&quot; to 1&quot;1/4)</li>
	<li>All pipework will be run in copper tube routed through floors and ceilings. Surface pipework will be clipped neatly.&nbsp;</li>
	<li>Any penetration through fire walls will be made good with the appropriate materials.&nbsp;</li>
	<li>Decorate any damaged ceiling areas.&nbsp;</li>
	<li>Site to be left clean and tidy.</li>
</ul>

<p><strong><u>Option 2</u></strong></p>

<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>Excavate area 600mm wide x 600mm depth in UPS room with a chase of about 500m to allow for perforated land drain.</li>
	<li>Supply &amp; fit cellar sump pump with chamber, lid and alarm box.</li>
	<li>Back fill with large gravel stones and concrete area.</li>
	<li>Electrical will be as above in option 1 ( connect mains high water alarm)</li>
	<li>Plumbing will be as above option 1 (pipe size 1&quot;1/4 to 1&quot;12)</li>
	<li>Site to be left clean and tidy.</li>
</ul>

<p>Project Note: Only 1 access hatch has been allowed for if more are required these will be of additional cost, there is currently no access to look above the ceiling this will be obtained once works have started to be carried out and will be obtainable&nbsp;once the first access hatch has been cut out. Upon visit for the survey access to ceiling was limited and could not locate local SVP to connect into, a provisional sum will be submitted for installation of 20m of pipework with fixture and fittings. This quote is based on the existing system are fit for new works to be connected to these.&nbsp;</p>
