<p>&nbsp;</p>

<p><strong>New toilet</strong></p>

<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>Remove block paving and set aside, excavate ground to expose existing drainage system.</li>
	<li>Install new 110mm plastic underground plpe work&nbsp;with new&nbsp;connections ready for new toilets.</li>
	<li>Install&nbsp;new inspection chamber.</li>
	<li>Make all necessary pipe work connections and test for correct working order.</li>
	<li>Incase all new pipe work in pea shingle.</li>
	<li>Make good around new inspection chamber and backfill in compacted layers.</li>
	<li>Re-lay set aside block paving to existing levels.</li>
</ul>

<p><strong>Carpentry</strong></p>

<ul>
	<li>Remove existing entrance door and door stops.</li>
	<li>Supply &amp; fit new 44mm door hung to open out onto corridor area, fitted with new stainless steel hinges with new D handle and push plate.</li>
	<li>Supply &amp; fit new door stops to existing door frame.</li>
	<li>Supply &amp; fit new door closer.</li>
	<li>Supply &amp; fit new gender neutral sign.</li>
	<li>Remove existing suspended ceiling.</li>
	<li>Supply and fit 75mm x 50mm timber stud walls to create 3no compartments.ot existing ceiling joists.</li>
	<li>Supply and fit 50mm acoustic insulation to new stud walls and clad all sides with tapered edge plasterboard.</li>
	<li>Tape and joint new plasterboard.</li>
	<li>Supply &amp; fit whiteroc hygienic sheeting to all walls up to height of 2.400mm.</li>
	<li>Supply &amp; Fit 2no new 44mm doors to new cubicles with&nbsp;stainless steel hinges,new handles and bathroom turn and release bolts.</li>
</ul>

<p><strong>Plumbing</strong></p>

<ul>
	<li>Supply &amp; fit new 600mm wide single convertor radiator to outside cubicle area,fixed to stud wall and connected to existing flow/return pipework in adjacent room.(seminar room )</li>
	<li>Supply and fit 2no new close coupled toilets within cubicles and connect waste to external drainage system.</li>
	<li>Supply and fit 2no small hand wash basins with mixer taps connect to existing supplies in adjacent disabled toilet and pipework to be run to new external gulley.</li>
</ul>

<p><strong>Electrics</strong></p>

<ul>
	<li>Core drill 2no new 4&quot; holes through brickwork ready for installation of 2no new extractor fans in each cubicle.</li>
	<li>Supply &amp; fit 4&quot; ducting and 2no new Vent axia&nbsp;extractor fans to be controlled by lighting circuit within each cubicle.</li>
	<li>Supply and fit new EM polo style lights controlled by 3 PIR&nbsp;switches 1 in each cubicle and 1 in toilet lobby. emergency self testing light in lobby area.</li>
	<li>Run new power supply from fuse board ready for installation of 2no new hand dryers.</li>
	<li>Supply and fit 2no new Lovair Air-fury hand dryers.</li>
</ul>

<p><strong>Ceilings</strong></p>

<ul>
	<li>Supply &amp; install 3no new small suspended ceilings with white ceiling tiles to 2no new toilet cubicles and toilet lobby area.</li>
</ul>

<p><strong>Flooring</strong></p>

<ul>
	<li>Remove existing floor covering.</li>
	<li>Supply and fit new cap and cove Altro contrax safety vinyl with thresholds to doorways. (Floor area 6.5m2)</li>
</ul>

<p><strong>Finishing</strong></p>

<ul>
	<li>Apply 2no coats of Dulux trade brilliant white eggshell above hygienic sheeting and to 3no new doors and door frames.</li>
	<li>Fit 2no soap dispensers and 2no paper towel dispensers and 2no toilet paper supplied by Goldsmiths.</li>
	<li>Supply &amp; fit 2no small mirrors above basins within cubicles.</li>
</ul>

<p><strong>Fire/smoke detectors</strong></p>

<ul>
	<li>To be carried out by others</li>
</ul>

<p><strong>Existing Disabled toilet</strong></p>

<ul>
	<li>Remove existing door.</li>
	<li>Supply &amp; fit new door (Min&nbsp;900mm wide in accordance of Doc M) hung on new stainless steel hinges with D-handles,push plate ,facility indicator bolts and clothes hook to back of door.</li>
	<li>Supply &amp; fit disabled and gender neutral toilet sign.</li>
	<li>Remove basin and set aside.</li>
	<li>Remove existing mirror above basin and set aside.</li>
	<li>Remove existing plastic wall cladding.</li>
	<li>Supply &amp; fit white plastic hygienic sheeting to all walls up to height of 2.4m.</li>
	<li>Supply and fit full length mirror.</li>
	<li>Remove existing WC and replace with new at required Doc M height,connected to existing waste pipework.</li>
</ul>

<p><strong>Flooring</strong></p>

<ul>
	<li>Remove existing floor covering.</li>
	<li>Supply and fit new cap and cove Altro contrax safety vinyl with thresholds to doorways. (Floor area 5.5m2)</li>
</ul>

<p><strong>Electrics</strong></p>

<ul>
	<li>Core drill new 4&quot; holes through brickwork ready for installation of 2no new extractor fans in each cubicle.</li>
	<li>Supply &amp; fit 4&quot; ducting and&nbsp; new Vent axia&nbsp;extractor fans to be controlled by lighting circuit.</li>
	<li>Supply and fit new EM polo style lights controlled by PIR switch with emergency function.</li>
	<li>Run new power supply from fuse board ready for installation of new hand dryer and disabled alarm.</li>
	<li>Supply and fit new Lovair Air-fury hand dryer.</li>
	<li>Supply &amp; fit new C-Tec&nbsp;Accessible Disabled persons toilet alarm kit NC951.</li>
</ul>

<p>Finishing</p>

<ul>
	<li>Apply 2no coats of Dulux trade brilliant white eggshell above hygienic sheeting and to&nbsp;new doors and door frame.</li>
	<li>Supply &amp; fit new brushed steel wall mounted grab rails and drop -down rails to Doc M contrast.</li>
	<li>Remove existing ceiling tiles and replace with new.</li>
	<li>Fit new soap dispensers,paper towel dispensers and toilet paper supplied by Goldsmiths.</li>
</ul>

<p>Seminar room</p>

<ul>
	<li>Supply &amp; fit new 75mm x 50mm timber studwork&nbsp;2.2m away fro existing wall to divide classroom into two separate rooms(seminar room and new toilet.</li>
	<li>New stud wall 2.9m wide x 3.8m high.</li>
	<li>Supply &amp; fit 50mm acoustic insulation to new stud wall and clad both sides with plasterboard.</li>
	<li>Tape &amp; joint new plasterboard.</li>
	<li>Cut out new opening in existing hallway&nbsp;wall to create new entrance from hallway into seminar room 1</li>
	<li>Supply &amp; fit new 44mm door and frame set to seminar room 1 entrance with 2no new handles&nbsp;</li>
	<li>Fit existing Kaba deadlock to new door.</li>
</ul>

<p><strong>Electrics</strong></p>

<ul>
	<li>Re-locate 3no existing double- sockets from new toilet into seminar room 1</li>
	<li>Re-locate 1no existing light switch from new toilet room into seminar room 1</li>
	<li>Remove existing&nbsp;emergency light fitting from toilet room and fit into seminar room 1</li>
	<li>Re-route data cables from media unit into new postilion.</li>
</ul>

<p><strong>Finishing</strong></p>

<ul>
	<li>Paint new stud wall only,new door frame&nbsp;and new door with brilliant white acrylic eggshell</li>
	<li>Make good to existing suspended ceiling with new wall track fixed to new stud wall.</li>
</ul>

<p>On completion transfer all waste from site and provide waste transfer note.</p>

<p>&nbsp;</p>

<p>&nbsp;</p>

<p>&nbsp;</p>
