<p>All existing emergency lights failed immediately upon testing and need to be replaced (this included 8W bulkheads throughout &amp;&nbsp;2no&nbsp;twin spots&nbsp;within the warehouse.)</p><ul><li>Mezzanine &ndash; (to install 1 no&nbsp;twinspot)</li><li>Warehouse &ndash; (to install 2 additional&nbsp;twinspots&nbsp;for coverage)</li><li>Currently no emergency lighting in main office and would have recessed LED units installed</li><li>Corridors have insufficient coverage and are non-compliant for change in direction &amp; require additional fittings.</li><li>All signage currently installed in non-compliant and needs to be changed to&nbsp;BS5266&nbsp;regulation standards.</li></ul><p>Areas were non-compliant for sufficient lux levels as follows:</p><ul><li>Operatives to apply protective sheeting to work routes and working areas.</li><li>Replace&nbsp;4no&nbsp;high bay high level&nbsp;400W&nbsp;HID lamps in warehouse.</li><li>Currently&nbsp;3no&nbsp;600*600 T8 lay in grid fittings worn and only partially working &ndash; to replace for new LED panels.</li><li>Dis-assemble &amp; remove racking in warehouse.</li><li>All new fittings to have appropriate cable &amp; fixings in compliance to&nbsp;BS5266&nbsp;&amp;&nbsp;BS7671.</li><li>All signage currently installed in non-compliant and needs to be changed to&nbsp;BS5266&nbsp;regulation standards.</li><li>Electrical certificate to be issued upon completion.&nbsp;</li><li>Site to be left clean and tidy.</li></ul><p>Our total cost to carry out the above works in normal working hours shall be &pound;2,345.77</p><p>Breakdown:</p><p>Labour: &pound;560.00</p><p>Materials: &pound;1,685.77</p><p>Electrical&nbsp;Certification: &pound;100.00</p>