<p>Access Control works:</p><p>To supply&amp; install new standalone access control systems to both male &amp; female W.Cs on site to control respective access.</p><p><br />Design is per door:</p><p>1no&nbsp;Standalone<br />Digital keypad c/w Integral Prox EMRFID prox reader.<br />1no Minimagnet c/w Z&amp;L bracket to open inwards.<br />1no Dome exit button (surface)<br />1no Green MCP (surface/resetable)<br />1no PSU/Ancillaries</p><p><br />Surface standalone digipad/reader to allow 1100 user codes and/or key fobs or cards for relay ONE, or secondary relay TWO 100 user codes and or key fobs or cards.</p><p><br />System comes with 20no Prox tags, additional tags available in 10PK &pound;40ea (plus carriage).</p><p>To egress toilets, green dome push to exit switch releases the magnet between 1to 99 secs (programmable).</p><p>In the event of an emergency a green break glass (MCP) installed beside the push to exit<br />switch internally directly disconnects the magnet supply leaving the magnet permanently deenergised.</p><p><br />If the client requires an interconnection with the site Fire Alarm system then an IO device allowing for a &quot;normally closed going open on Fire&quot; set of contacts would be required to be installed by others within the vicinity of the PSU we install, however the green MCP would be considered sufficient to BS58391:2013.</p><p><br />Cabling to each cupboard surface mounted&nbsp;in white PVC MT containment, unless ceiling access is easily permissible.</p><p><br />Cabling to external digipad/reader back entry from W.C containment.</p><p><br />As door is inward opening the Z&amp;L bracket may decrease the door opening by around 100mm at full leaf extent, however as there is already a door stop this may be minimal.</p><p>PSU to be located in electrical cupboard within W.Cs respectively.</p><p><br />Installation of 13amp FCU&nbsp; in W.C electrical cupboard&nbsp;for connection to our new PSU,&nbsp;provided a spare way is available on the local distribution board.</p><p><br />Programming &amp; training on completion allowed for.</p><p><br />Our total to carry out the above scope of works out of working hours shall be: &pound;3545.80 + VAT</p><p>Please see cost breakdown below:&nbsp;</p><p>Labour: &pound;1140.00</p><p>Materials: &pound;2325.8</p><p>Protection: &pound;80.00</p><p>&nbsp;</p><p>&nbsp;</p><p>&nbsp;</p><p>&nbsp;</p>