<ul>
	<li>Attended site 28/11/20, associated with Q11474.</li>
	<li>Operative applied&nbsp;protective sheeting to work routes and working areas.</li>
	<li>Upon attendance, operative discovered lights were out in the ground floor gent&#39;s toilets.</li>
	<li>Removed existing damage lamp fitting.</li>
	<li>Reinstalled new lamp to the fitting with new materials provided onsite.</li>
	<li>Tested and inspected in correct working order.</li>
	<li>Site was left clean and tidy.</li>
</ul>
