<p><strong>Car park&nbsp;</strong></p>

<ul>
	<li>Currently 2 columns with no power to them and are in a bad condition. Further investigation required. If power is unable to be reinstated then we recommend to install a new supply in FP cabling from one of the existing working wall lights. Approx. 30M - 40M of clipped direct FP cable required.&nbsp;</li>
	<li>Both columns need new isolation/cutouts, new cabling to lamp head and new LED lamps.&nbsp;</li>
</ul>

<p>&nbsp;</p>

<p><strong>Outside Sports Court&nbsp;</strong></p>

<ul>
	<li>There is currently 3x single columns and 3 x double columns. All have power to them but are in bad condition and some intermittently work. We recommend new isolators/cutouts, new cabling to flood lights from cut out and new 100w LED flood lights installed (9 in total).</li>
</ul>

<p><strong>Walkway</strong></p>

<ul>
	<li>High level floor light not working. The power is ok but the light fitting needs replacing. We recommend a new 100w LED flood light to be installed.&nbsp;</li>
	<li>Small column not working. The power is on but a new isolators/cutout, and new cabling to lamp head and new LED lamp to be installed.&nbsp;</li>
</ul>

<p><strong>Adventure Playground</strong></p>

<p>There is currently 2x single columns. All have power to them but are in bad condition and some intermittently work. We recommend new isolators/cutouts and new cabling to flood lights from cut out and new 100w LED flood lights installed (4 in total).&nbsp;</p>

<p>The ground is all different terrain and we would need a cherry picker a 7m working platform and triple extension ladders to complete these works.&nbsp;</p>

<p>&nbsp;</p>
