<p>-----Original Message-----<br />From: Luke Perry<br />Sent: 01 September 2017 09:30<br />To: HelpDesk<br />Subject: Q5703- scope of works</p><p>For this job the scope of works will be as followed:</p><p>&bull;sign in to site</p><p>&bull;make sure all operatives have read and signed the RAMS</p><p>&bull;isolate the water supply at a point to cause the least disruption.</p><p>&bull;drill a hole in the floor on the first floor where the water cooler is intended to be placed.</p><p>&bull;Run pipework through the drilled hole and along ground floor ceiling (battery room) (above false ceiling) also before installing pipework through the floor insert 20mm pipe to act as a conduit for the 15mm pipework.</p><p>&bull; connect to the water supply that is above ceiling feeding a sink with a 15mm tee also add a non return valve to the pipework going to the sink.</p><p>&bull; connect a washing machine valve to the end where the water cooler is intended to go.</p><p>&bull;insulate all pipework.</p><p>&bull; install a double socket on the wall where water cooler is intended to go.</p><p>&bull;install trunking to wall from socket to a local socket point</p><p>&bull;install cable within trunking and install a plug top to cable to cause minimal disruption.</p><p>&bull;clean and tidy site.</p><p>&bull;complete a worksheet.</p><p>&bull;sign out of site.</p><p>&nbsp;</p><p>This job will require:</p><p>2x operatives with electrical and plumbing skills between them.</p><p>&nbsp;</p><p>This job will require:</p><p>&nbsp;</p><p>1x day to complete.</p><p>&nbsp;</p><p>The materials required are:</p><p>1x 15mm soldered ring tee</p><p>3x 15mm solder ring elbows</p><p>3x lengths 3m 15mm copper pipe</p><p>3x 15mm solder ring couplers</p><p>1x washing machine valve</p><p>2 x non return valve</p><p>10m of 15mm pipe insulation</p><p>15x 15mm pipe clips</p><p>1x double socket with pattress</p><p>2x lengths mt2 self adhesive</p><p>15m 2.5m flex</p><p>1x plug top</p><p>1x 25mm drill bit (500mm in length)</p><p>1m 20mm plastic pipe (to act as conduit for pipe within concrete floor)</p><p>Thanks</p><p>Luke Perry</p>