<ul><li>Air conditioning engineer attended site 13th&nbsp;July and&nbsp;commission the Toshiba on site&nbsp;following the remedial works to drop the power from 290v to 240v at power station, Enfield. It was identified that there was no power to the remote controller due to the PCB in the indoor unit failing. It was recommended that both the indoor and outdoor units are replaced - the existing pipe work can be re-used, de-gas the existing and dispose of and install new.</li><li>To decommission, isolate and dispose of existing indoor and outdoor unit due to electrical fault on PCB board which has caused a catastrophic failure on the FCU, including recovery cylinder and disposal.</li><li>To supply and install 1 no. TOSH 12.3KW DIGI INV O/D RAV-SM1404ATP-E</li><li>To supply and install 1 no. TOSHIBA 3PH SUPER DIGITAL 12.5KW OUTDOOR</li><li>To supply and install 1 no. TOSHIBA RBC-AMS41E RC WITH 7 DAY TIMER</li><li>Installation of the above including Oxygen free nitrogen, recovery testing and commissioning.&nbsp;</li><li>Site to be left clean and tidy.</li></ul><p>Our total cost to carry out the above works in normal working hours shall be &pound;8,509.05+VAT</p><p><strong>Breakdown</strong></p><p>?Labour: &pound;2,520.00+VAT</p><p>Materials: &pound;4,189.05+VAT</p><p>Testing and commissioning - &pound;850.00+VAT</p><p>Decom and waste removal - &pound;795.00+VAT</p><p>Plant and machinery - &pound;155.00+VAT</p>