<ul><li>To attend site and don full orange PPE.</li><li>To go directly to platform 4 offices and sign in.</li><li>To undertake all required inductions, safety briefings and obtain all permits and permissions.</li><li>To obtain the key to room 19.</li><li>Ensure the asbestos management report is visited.</li><li>Operatives will set up a trifold barrier within the corridor leading from door 19, with safety signage clearly displaying danger 240V no unauthorised access.</li><li>Operatives will access distribution board AB and review the circuit chart to ensure the correct circuit is isolated.</li><li>The required breaker will be switched off, a second operative will verify the isolation at the field end using calibrated test equipment proven on a known source.&nbsp;</li><li>Once verified the circuit will be locked off.&nbsp; The cover of the distribution board will be removed.&nbsp;</li><li>The cables will then be sympathetically removed from the dedicated breaker and made safe via an enclosed cable connector.&nbsp; The cables will then be labelled detailing their function.</li><li>Where practicable to do so all redundant cable will be removed.</li><li>The distribution board cover will be carefully replaced ensuring no cables are trapped.</li><li>The circuit chart will be remarked to designate the MCB as spare.</li><li>The lock off tag off kit will be removed and the breaker left in the off position.</li><li>The door to the cupboard will be locked and the trifold&nbsp;barriers removed.</li><li>The area will be left clean and tidy.</li><li>Door 19 will be closed and an operative will remain at the door until the station representative is informed that works are complete and the door is locked.</li><li>Operatives will return to the office on platform 4 where all permits and permissions will be signed off.</li><li>Operatives will sign out.</li></ul><p><strong>PROJECT NOTES:</strong></p><p>The above works have been costed based on 8 hour shift&nbsp;working out of hours.</p><p>It is assumed that we have free access to all distribution boards and the client is aware that power will be going off at random intervals.</p><p>It is assumed that the site will be secure of the public during works.</p><p>Price does not include removal&nbsp;of any&nbsp;cabling.&nbsp;</p><p>Our total cost to carry out the above works&nbsp;out of normal working hours shall be +VAT</p>