<p>To install new hand dryers&nbsp;to disabled toilets.</p><ul><li>Operatives to apply protection to working areas and routes.</li><li>Remove existing hand towel dispensers and remove from site for safe disposal.</li><li>Install access hatches into plasterboard ceilings where required.</li><li>Supply and install new stainless steel cover plates.</li><li>Supply and install 14 no&nbsp;Dyson v type hand dryers.</li><li>Supply and install new 4 mm FP 200&nbsp;cable clipped to existing containment.</li><li>Supply and install new single gang dry lining back box to be installed within ceiling&nbsp;area.</li><li>Supply and install new FP 200 cable to be installed to the new double pole 13 A switched fused spur.</li><li>Hand dryer to be installed and cable terminated making sure all cable core are clearly identified and terminations mechanically sound.</li><li>New Double pole 13 A switched fused spur front to be installed.</li><li>Distribution board to be isolated by CBRE engineers.</li><li>FP200 cable to be installed and dressed into the existing distribution board.</li><li>New circuit to have all required dead tests carried out and result recorded.</li><li>Cable to be terminated to new RCBO ( if an RCBO cannot be installed in the existing distribution board then a standard MCB will have to be fitted and the DP switched spur will have to be replaced for a 30mA RCD DP switched fused spur)</li><li>Circuit to be energized and all required live tests to be carried out and results recorded.</li><li>Function tests to be carried out.</li><li>All Circuit components to be labelled which will indicate the distribution board and circuit reference.</li><li>Distribution board circuit chart to be updated.</li><li>Issue&nbsp;NIC EIC electrical installation certificate.</li><li>On completion leave work area in clean and tidy condition.</li></ul><p>&nbsp;</p><p>Our total cost to carry out the above works in / out of normal working hours shall be</p>