<p><strong>Automated door closers to run a supply only.</strong></p><ul><li>Install containment between doors and local distribution board (2&rdquo; cable tray fixed direct to ceiling slab).</li><li>Install single plasterboard boxes near where closers will be located.</li><li>Run 2.5mm fp200 (check spec of closers first) from DB and plasterboard boxes.</li><li>Install 16a RCBO within distribution board.</li><li>Dead test.</li><li>Terminate both spurs.</li><li>Terminate cable within DB to RCBO.</li><li>Complete live test.</li></ul><p>N.B. Closers to be installed by others.</p><p>&nbsp;</p><p><strong>Draught excluder and window film Installation.</strong></p><ul><li>Sign in to site.</li><li>Open window.</li><li>Stick excluder to window lip.</li><li>Close window.</li><li>Cut film to size.</li><li>Apply window film.</li><li>Clean site and sign out.</li></ul><p>&nbsp;</p><p><strong>Vision Panel within the door:</strong></p><ul><li>Cut out a section of the door (500mmx1500mm)</li><li>Install beading on one side.</li><li>Insert glass within door.</li><li>Insert glazing wedges or silicone.</li><li>Insert other bead around other side.</li></ul><p>&nbsp;</p><p><strong>Call point will be:</strong></p><ul><li>Lay protection where needed.</li><li>To install a non-switched spur from the automated door circuit.</li><li>To connect outside alarm/controller to the spur.</li><li>Install all call points and alarms where client specifies.</li><li>Connect all call points to the controller.</li></ul><p>&nbsp;</p><p>Our total cost to carry out the above works in&nbsp;normal working hours shall be &pound;5,194.80</p><p>Breakdown:</p><p>Labour: &pound;3,640.00</p><p>Materials: &pound;1,554.80</p>