<p>it is assumed that the work area will be cleared by others of all equipment prior to GDC attending site</p><ul><li>Operatives to attend site and sign in</li><li>IPAF operative to take delivery of boom lift.</li><li>signage and barriers to be installed around machinary</li><li>electrician with IPAF&nbsp;cert to install 4&quot; cable tray at high level from ground floor distribution board to new distribution woard within the 1st floor office</li><li>25mm 3 core steel&nbsp;wire armoured&nbsp;cable&nbsp;to be installed on the newly installed tray ( metal ties to be used every 1000mm)</li><li>1 no. metal clad 6 way distribution board to be installed high level in office ( area was agred on site survey)</li><li>new 63A mcb bs 60898 to be installed within existing distribution board</li><li>sub main to be terminated both end and tested prior to being energised</li><li>new containment to be installed within office ( 3 compartment dado trunking to wrapp&nbsp;the perimeter walls)</li><li>12 no. double socket back boxes to be installed&nbsp;</li><li>3 no. single back boxes to be installed ( for data points done by others)</li><li>3 no. switched fused spurs top be installed for low level wall panel convector heaters ( 3KW)</li><li>all wiring to be carried out using single core cables</li><li>wiring to have all required testing carried out and results recorded</li><li>all newly installed equipment to have labelling installed to reflect the circuit supply reference</li><li>Site to be left clean and tidy.</li></ul><p>Our total cost to carry out the above works in&nbsp;normal working hours shall be &pound;5,562.50+VAT</p><p>BREAKDOWN</p><p>Labour - &pound;3,000.00+VAT</p><p>Materials - &pound;2,562.50+VAT</p>