<p>Operatives to attend site and sign in.</p><p>All required isolation to be in place.</p><p>Site protection to be installed</p><p>Reclaim refrigerant from system.</p><p>Cut back pipe work at condenser side and dispose of old Filter drier and burn out drier.</p><p>Drill anchors into wall and hang existing williams condenser at low level off the floor.</p><p>Braze in new pipe work and filter drier and connect to condenser in new position.</p><p>Disconnect fridge pipe work and control cables and remove old Searle evaporator unit from within the walk in fridge, cut out old expansion valve. Braze in new expansion valve.</p><p>Hang new Searle tec4-5 evaporator and reconnect pipe work and cable. Pressure test system pipe work from condenser with OFN. Evacuate pipe work and charge with reclaimed refrigerant.</p><p>control panel to be replaced or existing components replaced (cost options below)</p><p>Run and check system.</p><p>site protection to be uplifted and site to be left clean</p><p>&nbsp;</p><p>&nbsp;</p><p>&nbsp;</p><p><strong>Cost Breakdown</strong></p><p><strong>Item 1 - evaporator replacement and condenser relocation works&nbsp;</strong></p><p><strong>Labour - &pound;880.00+VAT</strong></p><p><strong>Materials - &pound;845.00+VAT</strong></p><p><strong>Protection - &pound;50.00+VAT</strong></p><p><strong>O&amp;M manual - &pound;180.00+VAT</strong></p><p><strong>Total: &pound;1,955.00</strong></p><p>&nbsp;</p><p><strong>Item 2 - option 1 control panel component replacements</strong></p><p><strong>Labour - &pound;386.00+VAT</strong></p><p><strong>Materials - &pound;425.25+VAT</strong></p><p><strong>Total:&nbsp;&pound;811.25</strong></p><p>&nbsp;</p><p><strong>Item 3 - option 2 control panel replacement (replaced with danfoss optim&nbsp;6.5A 1ph)</strong></p><p><strong>Labour - &pound;386.00+VAT</strong></p><p><strong>Materials -&pound;356.00+VAT (control&nbsp;panel&nbsp;pdf will be attached with quotation)</strong></p><p><strong>Total: &pound;742.00</strong></p>