<p><strong>Area 1 - Gutter above East/West Reception - See page 1 of photo Report</strong></p><p>There is a leak above the doors, this is directly below a gutter which has been upgraded with a liquid coating system.&nbsp;</p><ul><li>To remove all debris from the gutter.&nbsp;</li><li>To carry out visual inspections to trace the source of the problem and carry out suitable repairs.&nbsp;</li></ul><p>Project Note: Access is via the external staircase and the roof has edge protection in place.&nbsp;</p><p>Our total cost to carry out the above works in normal working hours shall be<strong> &pound;915.50</strong></p><p>Breakdown:</p><p>Labour: &pound;560.00</p><p>Materials: &pound;357.50</p><p><strong>Area 2 - 2nd Floor Kitchen Duct - See page 2 of photo Report&nbsp;</strong></p><p>There is a leak around a duct into the kitchen, the original asphalt&nbsp;roof has been overlaid with a EPDM single ply membrane, there is no obvious defect around the duct.&nbsp;</p><ul><li>Remove all debris and clean the local area around the duct and carry out a thorough visual inspection, any splits or defective laps are to be repaired by:</li><li>Using a specialist cleaning fluid prepare the area.&nbsp;</li><li>Apply a patch repair compatible with the EPDM membrane.&nbsp;</li><li>Whilst&nbsp;on the roof we will re-fix the EPDM where it has pulled away from the upstand.&nbsp;</li><li>To patch repair the noticeable defect near the plant room.&nbsp;</li></ul><p>Our total cost to carry out the above works in normal working hours shall be <strong>&pound;1,320.50</strong></p><p>Breakdown:</p><p>Labour: &pound;840.00</p><p>Materials: &pound;480.50</p><p><strong>Area 3 - 4th Floor West Wing - See Page 3 of Photo Report</strong></p><p>There is a persistent leak below the outer wall of the lift shaft, the roof is weathered with a mineral surface felt and and te area of concern has been subject to several repairs, small sections of rendering need to be removed and replaced and suspect coping joints repaired.&nbsp;</p><ul><li>Clean off the roof area between the lift shaft and the parapet wall, a run of approx 16m.&nbsp;</li><li>Check and repair any small defects in the felt membrane.&nbsp;</li><li>Apply to this area and all upstands and associated roofing details within it one coat of Aquashield High build a high performance coating compound. &quot;Aquashield&quot; has a one-component polymeric gel composition with fibreflex. This compound contains no bituminous materials, which enables the product to stay permanently flexible.&nbsp;</li><li>Remove defective patches of render above the upstand that have been repaired using a mastic.&nbsp;</li><li>Apply a suitable render primer and re-render using a sand and cement mix. (no allowance for painting).&nbsp;</li><li>At the far end of the roof several large upstands have pulled away.&nbsp;</li><li>Remove defective upstands, prepare the area and install new, torch-applied, high performance felt upstands with a mineral surface finish.&nbsp;</li><li>To check the general roof area and repairing defects, loose laps and blisters.&nbsp;</li><li>All defects will be cut out, the area primed then a torch-applied felt patch applied.&nbsp;</li><li>A mobile man anchor unit will be used together with safety harnesses to carry out the works safely.</li></ul><p>Our total cost to carry out the above works in normal working hours shall be <strong>&pound;2,780.50</strong></p><p>Breakdown:</p><p>Labour: &pound;1,400.00</p><p>Materials: &pound;1,130.50</p><p>Access Equipment: &pound;250.00</p><p><strong>Area 4 M - Spur Roof - See page 4 of Photo Report&nbsp;</strong></p><p>There is a leak below the water tank upstand, this is an inverted felt roof, with insulation, slabs and pebbles laid over the felt.</p><ul><li>Remove and set aside the insulation, slabs and pebbles to expose a minimum 500mm of the&nbsp;flat roof area along the upstand.&nbsp;</li><li>Lift the lead cover flasing, prime the upstand and exposed flat roof and install a new torch-applied, high performance felt upstand, reinstate the insulation, pebbles and slabs.&nbsp;</li><li>Whilst on the roof, reinstate the section of fallen away sections of lead cover flashing.&nbsp;</li><li>A mobile man anchor unit will be used together with safety harnesses to carry out the works safely.&nbsp;</li></ul><p>Our total cost to carry out the above works in normal working hours shall be <strong>&pound;2,169.50</strong></p><p>Breakdown:</p><p>Labour: &pound;840.00</p><p>Materials: &pound;1,079.50</p><p>Access Equipment: &pound;250.00</p><p>The prices quoted above for the separate items are each independently valid, to enable the works to be done in stages, or as separate contracts if preferred. However, should you require all of the works carried out as on contract, we are able to offer a reduction on the total cost.&nbsp;</p><p>Project Note: We would carry out these works and providing that we can trace the points of ingress, we would carry out patch repairs. We are unable to provide a guarantee,&nbsp; should the patch repairs prove not successful&nbsp;it would be likely that extensive repairs would be required, if this is the case we would advise and provide recommendations.&nbsp;</p>