<p>We recommended a full site fire stopping survey to be carried&nbsp;out throughout&nbsp;the building</p>

<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
</ul>

<p><strong>&nbsp; First floor Electrical cupboard</strong></p>

<ul>
	<li>Commence with the installation of fire barriers to min&nbsp;30min&nbsp;fire stopping around the cables, pipes, cable tray, top of the wall and inside the trunking within electrical cupboard.</li>
	<li>The plasterboard is not marked as fire rated plasterboard and there are various gaps between the wall and the plasterboard, also where the cables penetrate through the wall.</li>
	<li>To replace the plasterboard with fire batt and seal around the cables with intumescent fire mastic and install a fire block&nbsp;inside the trunking.</li>
</ul>

<p><strong>Sports hall electric riser.</strong></p>

<ul>
	<li>Commence with the installation of fire barriers to min&nbsp;30min&nbsp;fire stopping around the pipework penetrations using collar and seal around cables.</li>
</ul>

<p><strong>Kitchen areas.</strong></p>

<ul>
	<li>The kitchen is not enclosed by fire resisting construction, the doors and shutter are not fire resistant, supply and install new fire rated equipment and Also we need to carry out fire stopping to all of the cables penetration and top of the walls within the kitchen areas.</li>
	<li>Site to be left clean and tidy.</li>
</ul>

<p>Our total cost to carry out the above works in&nbsp;normal working hours shall be &pound;6,308.00</p>

<p>Breakdown:</p>

<p>Labour: &pound;1,753.60 (2 operatives x 4 days).&nbsp;</p>

<p>Materials: &pound;4,404.40 (Fire batts - &pound;298.50, mastics - &pound;167.00, sealants - &pound;176.00, Cable collar pipe - &pound;197.00, roller shutter fire rated hatches - &pound;3,525.90, Protection - &pound;40.00).</p>

<p>Waste: &pound;150.00</p>

<p><strong>&nbsp; &nbsp; &nbsp; &nbsp;&nbsp;</strong></p>

<p><strong>&nbsp; &nbsp; &nbsp; &nbsp; &nbsp;&nbsp;</strong></p>

<p>&nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp;&nbsp;</p>

<p>&nbsp;</p>
