<p>Title of quotation - &nbsp;Bracken House Fan Coil Unit Installation<u1:p></u1:p></p>

<p><u1:p>&nbsp;</u1:p><u>Introduction<u1:p></u1:p></u><br />
Further to your recent enquiry and site survey we have great pleasure in submitting our<u1:p></u1:p>&nbsp;quotation for<u1:p></u1:p><br />
The Financial Times<u1:p></u1:p><br />
Bracken House<u1:p></u1:p><br />
1 Friday Street,<u1:p></u1:p><br />
London<u1:p></u1:p><br />
EC4M 9JA .<u1:p></u1:p></p>

<p><u>Scope <u1:p></u1:p></u><u1:p><br />
Costs i</u1:p>nclude the supply and installation of a new cooling only Dunham-Bush FCU&rsquo; system, new&nbsp;<u1:p></u1:p>CCW pipework c/w connections to the existing East and West riser pipework, new condensate<u1:p></u1:p>&nbsp;pipework, connections to new underfloor ductwork, plenums, supply and return floor linear<u1:p></u1:p>&nbsp;diffusers, pipe work flush &amp; clean and commissioning of system.<br />
Included are &nbsp;costs relating to the bespoke wall mounted FCU controller and BMS integration.<u1:p></u1:p>&nbsp;These items are to be supplied by the existing supplier to Bracken House Eon.</p>

<p><u1:p></u1:p></p>

<p><u>Scope of our works:</u><u1:p></u1:p><br />
Lift up floor carpet tiles and floating flooring to access void where required.<u1:p></u1:p><br />
Installation of 7&nbsp;no of Dunham Bush Cougar fan coil units to support systems 5&nbsp;no to small<u1:p></u1:p><br />
meeting rooms and 2 no to the large meeting room.<u1:p></u1:p><br />
Installation of a pipe work support system within under floor void.<u1:p></u1:p><br />
Installation of chilled water flow and return pipe work from local plant area.<u1:p></u1:p><br />
Installation of heating LTHW flow and return pipe work from local plant area.<u1:p></u1:p><br />
Insulation of all pipe work services installed</p>

<p><u1:p></u1:p></p>

<p>Installation of all mechanical items to facilitate the installation of fan coil units to include<u1:p></u1:p>&nbsp;strainers, commissioning sets check valves and isolation valves.<br />
Installation of supply and return air arrangements from each fan coil unit served by stainless<u1:p></u1:p>&nbsp;steel linear grilles to include ducting and insulation, linear grilles to be cut into floor tiles and<u1:p></u1:p>&nbsp;recessed.<br />
Installation of a fresh air duct work arrangement to serve each of the 7&nbsp;no fan coil units, the<u1:p></u1:p>&nbsp;fresh duct work will be taken from the riser duct work on the same floor, VCD&#39;d will be fitted for<u1:p></u1:p>&nbsp;balancing.<br />
Installation of 7&nbsp;no of condensate pumps and a dedicated copper condensate line.<br />
On&nbsp;<u1:p></u1:p>practical completion the pipe work and fan coil installation will be pressure tested, back filled<u1:p></u1:p><br />
and witnessed and approved before being opened to the main heating and cooling plant.</p>

<p>Commissioning of water and air systems, handover to the client.<br />
Tagging of valves and identification labelling to all services.<br />
Local Fan Coil Controls.<br />
Electrical Installation Works.</p>

<p><u>Cost includes:<u1:p></u1:p></u><br />
Protection of all transit routes, fixtures and fittings.</p>

<p>All required general builders works holes<u1:p></u1:p><br />
Diamond core drilling works from rear of riser area to floor area<u1:p></u1:p><br />
Certificated fire stopping to all penetrations created during these works<u1:p></u1:p><br />
All waste removal and relocation for safe disposal.<u1:p></u1:p><br />
CAD Drawing of new system - (To be added to existing drawings).<u1:p></u1:p></p>

<p><br />
&nbsp;<br />
<br />
Our costs to undertake these works out of hours will be:<u1:p></u1:p></p>

<p><u1:p>&nbsp;</u1:p>&pound;131,990.00<br />
<br />
<u>Ductwork Specification</u></p>

<p><u><u1:p></u1:p></u></p>

<p>All ductwork will comply with DW144 and will be supplied in Spiral Aluminium unless specified by project details.<u1:p></u1:p><br />
Ductwork on this project will be fire rated.<br />
&nbsp;</p>

<p>Condensate drainage Specification<u1:p></u1:p><br />
A new condensate removal pipe work system will be arranged to facilitate the removal of<u1:p></u1:p>&nbsp;condensate from the new indoor unit to the existing internal drain termination points,as<u1:p></u1:p>&nbsp;required. Generally, the condensate pipe work will be gravity type, however, in some instance pumps will be fitted to facilitate the removal of the condensate water from the indoor fan coil units.<br />
<br />
Interconnecting cables &amp; Controls Specification<u1:p></u1:p><br />
Where required all interconnecting power and control cables will generally be routed along with&nbsp;<u1:p></u1:p>the refrigerant pipe / Ductwork and be adequately supported, in accordance with the relevant<u1:p></u1:p>&nbsp;installation regulations.</p>

<p><u1:p></u1:p></p>

<p>&nbsp;The indoor fan coil unit(s) shall be controlled via a locally mounted remote controller, allowing -3 / +3 of set temperature.</p>

<p>Upon practical completion of the refrigeration &amp; electrical/controls works, we would then<u1:p></u1:p>&nbsp;commission the installation. The refrigerant pipe work would be pressure tested and strength<u1:p></u1:p>&nbsp;tested to ensure a leak tight system and evacuated to remove air and moisture.</p>

<p><u1:p></u1:p></p>

<p>The installation would be charged so correct operating pressures ascertained. We would complete<u1:p></u1:p>&nbsp;the installation by checking: electrics, pipe work, condensate removal systems, all available<u1:p></u1:p>&nbsp;functions and settings. Finally, the whole system would be demonstrated or witness tested to the on-site<u1:p></u1:p>&nbsp;representative.<u1:p></u1:p></p>

<p><u1:p></u1:p></p>

<p><u1:p></u1:p></p>

<p><u1:p></u1:p></p>

<p><u1:p></u1:p></p>
