<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>Supply&nbsp;&amp;&nbsp;install&nbsp;Midea&nbsp;air&nbsp;conditioning&nbsp;system&nbsp;based&nbsp;on&nbsp;current&nbsp;heat&nbsp;recovery&nbsp;VRF&nbsp;systems&nbsp;cooling duty&nbsp;to&nbsp;existing&nbsp;as&nbsp;installed&nbsp;site&nbsp;evaporators&nbsp;quantity. VRF&nbsp;HEAT&nbsp;RECOVERY&nbsp;system 2nd&nbsp;Floor&nbsp;(AC01&shy;AC03) 2no:&nbsp;2.2kW&nbsp;Heat&nbsp;Pump&nbsp;(Cooling&nbsp;&amp;&nbsp;Heating)&nbsp;Wall&nbsp;Mount&nbsp;Units 1no:&nbsp;4.5kW&nbsp;Heat&nbsp;Pump&nbsp;(Cooling&nbsp;&amp;&nbsp;Heating)&nbsp;Wall&nbsp;Mount&nbsp;Unit 1st&nbsp;Floor&nbsp;(AC04&shy;AC13) 5no:&nbsp;3.6kW&nbsp;Heat&nbsp;Pump&nbsp;(Cooling&nbsp;&amp;&nbsp;Heating)&nbsp;Compact&nbsp;Cassette&nbsp;Units 5no:&nbsp;8kW&nbsp;Heat&nbsp;Pump&nbsp;(Cooling&nbsp;&amp;&nbsp;Heating)&nbsp;4&nbsp;Way&nbsp;Cassette&nbsp;Units Ground&nbsp;Floor&nbsp;(AC14&shy;AC22) 3no:&nbsp;3.6kW&nbsp;Heat&nbsp;Pump&nbsp;(Cooling&nbsp;&amp;&nbsp;Heating)&nbsp;Compact&nbsp;Cassette&nbsp;Units 6no:&nbsp;8kW&nbsp;Heat&nbsp;Pump&nbsp;(Cooling&nbsp;&amp;&nbsp;Heating)&nbsp;4&nbsp;Way&nbsp;Cassette&nbsp;Units Ground&nbsp;to&nbsp;2nd&nbsp;Floor&nbsp;(in&nbsp;ceiling) 4no:&nbsp;4way&nbsp;MS&nbsp;branch&nbsp;boxes 2no:&nbsp;6way&nbsp;MS&nbsp;branch&nbsp;boxes ALL&nbsp;VRF&nbsp;EVAPORATOR&nbsp;UNITS&nbsp;ABOVE&nbsp;SERVED&nbsp;BY&nbsp;BELOW:&nbsp;&shy; 2no&nbsp;3PH&nbsp;HEAT&nbsp;RECOVERY&nbsp;45kW&nbsp;R410a&nbsp;outdoor&nbsp;units&nbsp;interconnected&nbsp;located&nbsp;to&nbsp;replace&nbsp;existing plant&nbsp;condensers. HEAT&nbsp;RECOVERY&nbsp;3&nbsp;pipe&nbsp;system&nbsp;allows&nbsp;for&nbsp;a&nbsp;dual&nbsp;mode&nbsp;of&nbsp;operation&nbsp;(heating&nbsp;or&nbsp;cooling)</li>
	<li>On completion uplit protective sheeting and leave work area in clean tidy condition</li>
</ul>
