<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>Operatives attended site and identified faulty wiring for the dining room lights</li>
	<li>Operatives rewired the lighting circuit from the wall lights to a new circuit (route agreed with home)</li>
	<li>Operatives tested and left dining lighting working as designed</li>
	<li>Operatives investigated the external lighting fault and have found moisture in multi boxes causing circuitry to trip</li>
	<li>Operatives have suggested installing new LED bulkhead lighting to return walls to replace the 2no existing lights (quotation to be&nbsp; submitted)</li>
	<li>Site to be left clean and tidy.</li>
</ul>
