<p><strong>Attended site on 21/6/19 to carry out intrusive survey on AC repairs:</strong></p>

<p><b>Job 1:&nbsp;</b><strong>Meeting room 3 - Unit 25</strong></p>

<ul>
	<li>Unit 25 has no power on indoor unit.&nbsp;</li>
	<li>Checked outdoor and isolator water damaged.</li>
	<li>Filled with water and all terminals are rusted.</li>
	<li>Replacement is required.</li>
	<li>Please see Q8947.</li>
</ul>

<p><strong>Job 2: 1st Floor Board Room - Unit 22</strong></p>

<ul>
	<li>Unit 22 is in correct working order, however maintenance is required.</li>
	<li>Please see Q8947.</li>
</ul>

<p><strong>Job 3: 1st Floor by Joe Greene - Unit 17</strong></p>

<ul>
	<li>Switched off at MCB and has no power.</li>
	<li>Turned on and the unit started working.</li>
	<li>Cleaned filter as no air flow is coming from the unit.</li>
	<li>Some of the terminals on outdoor isolator are rusty, potentially had water in but when checked was dry.</li>
</ul>

<p><b>Job 4: 1st Floor by Nathan Maybuty - Unit 13</b></p>

<ul>
	<li>Tested and all in correct, working order.</li>
	<li>Filters are really dirty and maintenance is required.</li>
	<li>Please see Q8947.</li>
</ul>

<p><b>Job 5: Ground Floor - Unit 1</b></p>

<ul>
	<li>Switched off on isolator.</li>
	<li>Turned on and in correct, working order.</li>
</ul>

<p><strong>Job 6: Kitchen 1st Floor - Unit 16</strong></p>

<ul>
	<li>Investigated unit and was working.</li>
	<li>Fan louver blade has snapped.</li>
	<li>Please see Q8947.</li>
</ul>

<p>&nbsp;</p>
