<p>We have been asked to check if the fire door integrity if is the same as before they install the mag lock.</p><p>They have to remove the old mag lock an install a new one on different location on the door, they patch repair the damage but the materials thy use are not fire rated.</p><p>&nbsp;</p><p>1. Holes on the door cover with soft wood We recommend to remove the soft wood and install an fire rated lipping and fill the edges with 2 parts intumescent filler.</p><p>2. Screw holes cover with wax.</p><p>Recommend to be fill with 2 parts intumescent filler 3. Doors are not closing flush Recommended to install intumescent pads behind the mag lock to allow the door to close flush</p><p>&nbsp;</p><p>We have found few other breaches and I fave attach a report, But they are not made from installation of mag lock , this quote are not including none of the other repairs. And we can not certify the doors until all the other bridges are completed.</p><p>&nbsp;</p><p>Materials required:</p><p>Fire rated lipping x 24&nbsp; at 2400x 18 x 45, and 24 at 2400x 4 x 45, oval wire nail, Wood filler natural colour x 5, wood chisel, sand paper sponge 120 x 8 Wax stick x 8 Hover, dust sheets x 4 Small ladder x 2 20mm brush seal x 40</p><p>&nbsp;</p><p>Labourer :</p><p>Over hours 3 man x 9 days.</p>