<p>it is assumed that the existing mccb panel has sufficient space for new cabling and the existing switch gear functions correctly</p><ul><li>This quotation has been compiled based on the following documentation / specifications:<br />&nbsp;Dwg 014.061.M00</li></ul><ul><li>Scope of Works<br />We have allowed for the following scope of works:<br />1. Power Cabling<br />2. Cable Management<br />3. Labeling &amp; Tagging<br />4. Cable Testing</li></ul><p><strong>1) Power Cabling</strong><br />We have allowed for the supply, installation and termination of the site run low voltage power cabling. We have allowed for the below cabling:</p><p><strong>FROM &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp;&nbsp;TO &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp;CABLE&nbsp;TYPE &nbsp; &nbsp; &nbsp; &nbsp;SIZE (MM) &nbsp; C</strong><strong>ORES &nbsp;&nbsp;NO.</strong><strong>&nbsp;CABLES &nbsp;&nbsp;LTH PER </strong><strong>CABLE (M)</strong></p><p>Existing basement&nbsp;MCCB Board &nbsp; &nbsp;Chiller No.2&nbsp; &nbsp; &nbsp; &nbsp; SWA &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp;120 &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; 4 &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp;2 &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp;80&nbsp;</p><p>Existing basement&nbsp;MCCB Board &nbsp; &nbsp;Chiller No.2 &nbsp; &nbsp; &nbsp; &nbsp;6491X&nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; 70 &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; 1 &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp;2 &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp; &nbsp;80</p><p>&nbsp;</p><p>Note: Any cable not shown on the above schedule is not included in our contract<br />We have allowed to re-terminate the existing 2No 4C 150mm to Chiller No.1 into the adjacent 400A Main Panel Section</p><p>Note: We have not allowed to remove any existing redundant cable for example existing cable to Chiller No.2 and Chiller No.1<br />&nbsp;</p><p><strong>2) Cable Management</strong><br />We have allowed for the supply and installation of Medium Duty Ladder supporting systems for the cabling within our scope of supply. This includes the below:<br />8th Floor from the Riser to Chiller No.1 and 2 mounted at high level<br />Note: We have assumed that the high level ladder can be installed using 2m towers<br />We have assumed the ladder is Medium Duty Type<br /><br /><strong>3) Labelling &amp; Tagging</strong><br />We have allowed for the labeling and tagging of all electrical equipment with our scope of supply / installation. This includes the labeling of all junction boxes, distribution boards etc.</p><p><strong>4) Cable Testing</strong><br />We have allowed for the completion of all cable testing associated with the items being supplied or installed by us.<br />We have allowed for the generation of all test certificates, completion of all tests and the provision of any necessary test equipment.<br />We have allowed for the completion, collation and presentation of the produced test documentation.</p><p>Exclusions from Scope of Supply<br />The following items are specifically excluded from our scope of supply:<br />Civil works other than minor holes for cable penetrations<br />Lightning Protection<br />Temporary Works<br />Removal of redundant Cabling/Equipment<br />Commissioning</p><p><br />Assumptions<br />We have assumed that we will have good unhindered access to the site for delivery and installation of all equipment.<br />We have assumed the existing containment system has suitable capacity for the new cables required by this project (Basement Area and Risers to 8th Floor only)<br />It is assumed the work will be carried out during a normal working week (Monday &ndash; Friday 07:00hrs - 17:00hrs) If weekend work and/or out of hours&rsquo; work is required this will be charged at additional cost.</p><p>We have assumed that the cable sizes shown on the Drawings issued at tender stage have been calculated correctly by others based on the Chiller Loadings and taking into account the correct cable rating factors.&nbsp;</p><p><strong>The total cost for these works in normal working hours are: &pound;16,038.47</strong></p><p><strong>Breakdown:</strong></p><p><strong>Labour:&nbsp;&pound;6,750.00+VAT</strong></p><p><strong>Materials: &pound;8,774.47+VAT</strong></p><p><strong>Access Equipment &amp; Plant: &pound;514.00+VAT</strong></p>