<p><strong>scope of works for Landlords board - 4/SW/2UPS</strong>?</p><ul><li>Existing isolated supplies ( from Deutsche&nbsp;bank ups boards)&nbsp;&nbsp;to landlord boards boards (4/SW/2UPS) to be removed and disposed of.</li><li>1 no. existing Landlords supply (4/SW2UPS) to be tested and proved fit for continue use, once proven fit for continued use the cable is to be terminated into Landlords board(4/SW2UPS)&nbsp;</li><li>Existing final circuits from Landlords distribution board&nbsp;(4/SW2UPS) to be removed and left in the riser cupboard.</li><li>Grommets to be installed into cut out holes where final circuits where removed.</li><li>Landlords tap off (4/SW/2UPS) to have the lock off kit removed and energised, live tests to be carried out and a certificate issued on completion.</li><li>Any floors uplifted to be reinstated( carpets to be left to one side to be disposed by others)</li><li>Fire Stopping to be installed where required.</li></ul><p><strong>scope of works for Landlords board&nbsp; - 4/SW/1UPS</strong>?</p><ul><li>Existing isolated supplies ( from&nbsp;Deutsche&nbsp;bank ups boards)&nbsp;&nbsp;to landlord boards boards (4/SW/2UPS) to be removed and disposed of.</li><li>1 no. new supply to be installed from the existing distribution board to the existing landlords tap&nbsp;off in the riser.</li><li>Supply cable to be SWA&nbsp;and clipped to existing containment where&nbsp; available.</li><li>Existing temporary supplies to fire alarm, emergency lighting and BMS panel to be removed and .</li><li>Existing final circuits from Landlords distribution board&nbsp;(4/SW1UPS) to be removed and left in the riser cupboard except for the fire alarm, emergency lighting and BMS circuits.</li><li>Landlords tap&nbsp;off&nbsp;(4/SW1UPS) to be energised and all required testing to be carried out.</li><li>A certificate will be issued on completion</li><li>any floors uplifted to be&nbsp;reinstated( carpets to be left to one side to be disposed by others)</li><li>Fire Stopping to be installed where required.</li></ul><p>Our total cost to carry out the above works out of normal working hours shall be &pound;5,207.79+VAT</p><p>Breakdown</p><p>Labour - &pound;4,632.00</p><p>Materials - &pound;325.79</p><p>Waste - &pound;250.00</p>