<p>Supply,&nbsp;installation&nbsp;&amp;&nbsp;commissioning&nbsp;(as&nbsp;detailed</p>

<p>&nbsp;</p>

<p>Supply&nbsp;&amp;&nbsp;install&nbsp;Midea&nbsp;air&nbsp;conditioning&nbsp;system&nbsp;based&nbsp;on&nbsp;tender&nbsp;specification. VRF&nbsp;HEAT&nbsp;PUMP&nbsp;system Consultation/Examination&nbsp;(AC01) 1no:&nbsp;4.5kW&nbsp;Heat&nbsp;Pump&nbsp;(Cooling&nbsp;&amp;&nbsp;Heating)&nbsp;Compact&nbsp;Cassette&nbsp;Unit Consultation/Examination&nbsp;(AC02) 1no:&nbsp;2.8kW&nbsp;Heat&nbsp;Pump&nbsp;(Cooling&nbsp;&amp;&nbsp;Heating)&nbsp;Compact&nbsp;Cassette&nbsp;Unit Microscopy&nbsp;Examination&nbsp;(AC07) 1no:&nbsp;2.2kW&nbsp;Heat&nbsp;Pump&nbsp;(Cooling&nbsp;&amp;&nbsp;Heating)&nbsp;Wall&nbsp;Mount&nbsp;Unit Corridor&nbsp;Waiting&nbsp;Area&nbsp;(AC03) 1no:&nbsp;1.7kW&nbsp;Heat&nbsp;Pump&nbsp;(Cooling&nbsp;&amp;&nbsp;Heating)&nbsp;Compact&nbsp;Cassette&nbsp;Unit Office/Reception&nbsp;(AC04) 1no:&nbsp;2.2kW&nbsp;Heat&nbsp;Pump&nbsp;(Cooling&nbsp;&amp;&nbsp;Heating)&nbsp;Wall&nbsp;Mount&nbsp;Unit Triage&nbsp;&amp;&nbsp;Bloods&nbsp;Room&nbsp;(AC06) 1no:&nbsp;2.2kW&nbsp;Heat&nbsp;Pump&nbsp;(Cooling&nbsp;&amp;&nbsp;Heating)&nbsp;Wall&nbsp;Mount&nbsp;Unit Store&nbsp;(AC05) 1no:&nbsp;2.2kW&nbsp;Heat&nbsp;Pump&nbsp;(Cooling&nbsp;&amp;&nbsp;Heating)&nbsp;Wall&nbsp;Mount&nbsp;Unit ALL&nbsp;VRF&nbsp;EVAPORATOR&nbsp;UNITS&nbsp;ABOVE&nbsp;SERVED&nbsp;BY&nbsp;BELOW:&nbsp;&shy; 1no&nbsp;1PH&nbsp;HEAT&nbsp;PUMP&nbsp;15.5kW&nbsp;R410a&nbsp;outdoor&nbsp;unit&nbsp;located&nbsp;in&nbsp;cage&nbsp;as&nbsp;per&nbsp;tender. HEAT&nbsp;PUMP&nbsp;2&nbsp;pipe&nbsp;system&nbsp;allows&nbsp;for&nbsp;a&nbsp;single&nbsp;mode&nbsp;of&nbsp;operation&nbsp;(heating&nbsp;or&nbsp;cooling),&nbsp;simultaneous modes&nbsp;of&nbsp;operation&nbsp;are&nbsp;prohibited,&nbsp;however&nbsp;units&nbsp;can&nbsp;have&nbsp;different&nbsp;set&nbsp;points.</p>

<p>10&nbsp;YEARS&nbsp;(VRF)&nbsp;PARTS&nbsp;WARRANTY&nbsp;INCLUDED&nbsp;on&nbsp;Midea&nbsp;air&shy;conditioning&nbsp;units&nbsp;subject&nbsp;to maintenance&nbsp;contract&nbsp;remitted&nbsp;with&nbsp;Annetech&nbsp;(GDC) for&nbsp;duration. Efficient&nbsp;inverter&nbsp;systems&nbsp;quoted&nbsp;as&nbsp;they&nbsp;are&nbsp;more&nbsp;environmentally&nbsp;friendly&nbsp;lowering&nbsp;running&nbsp;costs&nbsp;&amp; extending&nbsp;system&nbsp;life. Units&nbsp;HEAT&nbsp;as&nbsp;well&nbsp;as&nbsp;COOL,&nbsp;you&nbsp;could&nbsp;expect&nbsp;the&nbsp;cost&nbsp;&amp;&nbsp;efficiency&nbsp;of&nbsp;the&nbsp;heating&nbsp;function&nbsp;to&nbsp;be&nbsp;a large&nbsp;benefit&nbsp;versus&nbsp;traditional&nbsp;heating&nbsp;methods&nbsp;(GAS&nbsp;etc.). Evaporator&nbsp;condensate&nbsp;drainage&nbsp;via&nbsp;corner&nbsp;trunking&nbsp;pumps&nbsp;systems&nbsp;for&nbsp;wall&nbsp;mounts&nbsp;&amp;&nbsp;gravity&nbsp;for compact&nbsp;cassettes&nbsp;to&nbsp;local&nbsp;waste. Condenser&nbsp;housing&nbsp;allowed&nbsp;for,&nbsp;please&nbsp;note&nbsp;right&nbsp;side&nbsp;may&nbsp;require&nbsp;modification&nbsp;due&nbsp;to&nbsp;limited&nbsp;space mounting&nbsp;on&nbsp;site. Condenser&nbsp;mounted&nbsp;on&nbsp;rubber&nbsp;channel&nbsp;mounts&nbsp;(Flexi&shy;foot&nbsp;style),&nbsp;winter&nbsp;operation&nbsp;condenser drainage&nbsp;gravity&nbsp;to&nbsp;ground&nbsp;locally&nbsp;at&nbsp;mounted&nbsp;position. Controls&nbsp;via&nbsp;hard&nbsp;wired&nbsp;remotes&nbsp;for&nbsp;all&nbsp;units&nbsp;as&nbsp;indicated&nbsp;on&nbsp;drawing. 1PH&nbsp;Electrical&nbsp;supply&nbsp;to&nbsp;both&nbsp;VRF&nbsp;condenser&nbsp;&amp;&nbsp;a&nbsp;separate&nbsp;1PH&nbsp;radial&nbsp;to&nbsp;serve&nbsp;VRF&nbsp;indoor&nbsp;units&nbsp;will be&nbsp;installed,&nbsp;power&nbsp;cabling&nbsp;installed&nbsp;on&nbsp;existing&nbsp;above&nbsp;ceiling&nbsp;containment&nbsp;or&nbsp;clipped&nbsp;direct&nbsp;in SWA/XPLE&nbsp;cable&nbsp;for&nbsp;all&nbsp;230V&nbsp;cabling. Controls&nbsp;&amp;&nbsp;interconnection&nbsp;cabling&nbsp;on&nbsp;existing&nbsp;above&nbsp;ceiling&nbsp;containment&nbsp;or&nbsp;new&nbsp;metal&nbsp;flexible clipped&nbsp;conduit&nbsp;where&nbsp;running&nbsp;to&nbsp;controller&nbsp;drops&nbsp;or&nbsp;evaporators&nbsp;for&nbsp;where&nbsp;no&nbsp;containment&nbsp;or available&nbsp;cable&nbsp;to&nbsp;be&nbsp;tied&nbsp;to&nbsp;exists On&nbsp;completion&nbsp;of&nbsp;works&nbsp;a&nbsp;works&nbsp;clean&nbsp;will&nbsp;be&nbsp;carried&nbsp;out,&nbsp;however&nbsp;as&nbsp;this&nbsp;is&nbsp;a&nbsp;medical&nbsp;surgery&nbsp;we would&nbsp;advise&nbsp;a&nbsp;deep&nbsp;or&nbsp;medical&nbsp;clean&nbsp;be&nbsp;carried&nbsp;out&nbsp;by&nbsp;others&nbsp;(not&nbsp;covered&nbsp;within&nbsp;this&nbsp;quotation).</p>

<p>Carry out minor fire stopping to new penetrations and certificate.</p>

<p>Any&nbsp;license&nbsp;applications&nbsp;etc.&nbsp;are&nbsp;the&nbsp;duty&nbsp;of&nbsp;the&nbsp;client. FGAS&nbsp;Certification&nbsp;included&nbsp;for&nbsp;within&nbsp;this&nbsp;quotation.</p>

<p>&nbsp;</p>
