<p><strong>North Side of Walkway</strong></p><ul><li>Operatives to apply protective sheeting to work routes</li><li>Commence with removing existing faulty roof lights and wiring fed from LP/RP-LPH ( gcm to be in place)</li><li>New 50mm cable tray to be inStalled around the perimeter of the roof top</li><li>New ip rated &nbsp;lights to be installed &nbsp;in existing lights positions</li><li>New 4 core 2.5mm fp200&nbsp;to be run on new tray from distribution board to new light fittings all holes made or used to be filled using intumescent fire mastic</li><li>6 no. new bulkheads to be installed with integral pir and&nbsp;&nbsp;day light sensors</li><li>4 no. emergency non maintained bulk heads to be installed</li><li>Key switch to be installed near distribution board for emergency lighting test</li><li>All required tests to be carried out and results recorded</li><li>Certificate to be issued on completion</li><li>Site to be left clean and tidy.</li></ul><p>Our total cost to carry out the above out of normal working hours shall be &pound;3,395.00+VAT</p><p>Breakdown</p><p>Labour - &pound;1,930.00+VAT ( 5 NO. ELECTRICIANS SHIFTS)</p><p>Materials - &pound;1,225.00+VAT</p><p>O&amp;M Manual - &pound;140.00+VAT</p><p>Waste - &pound;100.00+VAT</p><p><strong>South Side of Walkway</strong></p><ul><li>Operatives to apply protective sheeting to work routes.</li><li>Commence with removing existing faulty roof lights and wiring fed from LP/RP-LPH (GCM to be in place)</li><li>New 50mm cable tray to be installed around the perimeter of the roof top</li><li>New ip rated lights to be installed in existing lights positions.</li><li>New 4 core 2.5mm fp200 to be run on new tray from distribution board to new light fittings all holes made or used to be filled using intumescent fire mastic.</li><li>6 no. new bulkheads to be installed with integral pir and day light sensors</li><li>4 no. emergency non maintained bulk heads to be installed</li><li>Key switch to be installed near distribution board for emergency lighting test</li><li>All required tests to be carried out and results recorded.</li><li>Certificate to be issued on completion.</li><li>Site to be left clean and tidy.</li></ul><p>Our total cost to carry out the above out of normal working hours shall be &pound;3,395.00 + VAT</p><p>Breakdown:</p><p>Labour: &pound;1,930.00 + VAT(5 NO. ELECTRICIANS SHIFTS)</p><p>Materials - &pound;1,225.00 + VAT</p><p>O&amp;M Manual - &pound;140.00 + VAT</p><p>Waste - &pound;100.00 + VAT</p>