<p><strong>Supply and install protection to floors and cabinets. Protection to be left in place for duration of works. Supply and install task lighting for duration of work Works to be carried done out of hours.</strong></p>

<p><strong>The required upgrade works for the SER to comply with the London Underground and Network Rail standards include but are not limited to:</strong><br />
- Relocation of existing lighting tracks and ancillaries.<br />
- Inspection, cleaning and relocation of existing T5 luminaires.<br />
- Mandatory re-lamping of existing T5 luminaires.<br />
- Extension of the existing lighting trunking towards the back of the room.<br />
- Supply and installation of new supplementary lighting tracks and ancillaries.<br />
- Supply and installation of new supplementary LED track luminaires.<br />
- T5 luminaires are discontinued, manufacturers only propose LED luminaires today.<br />
- Supply and installation of new supplementary LED suspended emergency luminaires.<br />
- Extension of the existing DB/L NEG R1/1L2 lighting circuit to include the new track feeder units.<br />
- Extension of the existing DB/LCBG R1/1L2 lighting circuit to include the new LED suspended emergency luminaires.<br />
- Testing and commissioning of the lighting installation - Updated of as-built and O&amp;M information.</p>

<p><strong>CER</strong><br />
- Supply and install protection to floors and cabinets. Protection to be left in place for duration of works.<br />
- Supply and install task lighting for duration of works.<br />
- Works to be carried done out of hours.</p>

<p><strong>The required upgrade works for the CER to comply with the London Underground and Network Rail standards include but are not limited to:</strong></p>

<p>- Relocation of existing lighting tracks and ancillaries - Inspection, cleaning and relocation of existing T5 luminaires.<br />
- Mandatory re-lamping of existing T5 luminaires.<br />
- Supply and installation of new lighting tracks and ancillaries.<br />
- Supply and installation of new supplementary LED track luminaires.<br />
- T5 luminaires are discontinued, manufacturers only propose LED luminaires today.<br />
- Supply and installation of new supplementary LED wall-mounted luminaires.<br />
- Supply and installation of new supplementary LED suspended emergency luminaires.<br />
- Extension of the existing DB/L NEG R1/2L2 lighting circuit to include the new track feeder unit and wall-mounted luminaires.<br />
- Extension of the existing DB/LCBG R1/2L2 lighting circuit to include the new LED suspended emergency luminaires.<br />
- Testing and commissioning of the lighting installation - Updated of as-built and O&amp;M information.</p>

<p><strong>Simulation Room The required upgrade works for the Simulation Room to switch separately the simulation and examiners area include but are not limited to:</strong><br />
- Supply and installation of new scene set module.<br />
- Update of project graphical database.<br />
&nbsp;</p>
