<ul>
	<li>To register the installation with IFCC portal.</li>
	<li>To attend site and undertake all required inductions.</li>
	<li>To obtain all required permits and permissions.</li>
	<li>To install protection to all required areas in the form of correx and low tack tape / carpet protector.</li>
	<li>To sympathetically uplift all required carpet tiles and set aside for reinstatement.</li>
	<li>To uplift floor tiles either side of the area requiring fire stopping and set aside for reinstatement.</li>
	<li>To prepare the required area for fire stopping.</li>
	<li>To install fire batts rated to 60 minutes.</li>
	<li>To seal with mastic rated to 60 minutes.</li>
	<li>To label installation.</li>
	<li>To undertake housekeeping to the area clearing all generated waste and debris.</li>
	<li>To reinstate previously uplifted floor tiles and carpet tiles.</li>
	<li>To uplift all installed protection.</li>
	<li>To obtain approval and sign off.</li>
	<li>Upon completion to issue certification.</li>
</ul>

<p>Note</p>

<ul>
	<li>To limit impact on occupants and day to day undertakings works are programmed at one room per out of hours shift to ensure minimal impact.</li>
	<li>No storage is accounted for on site, all plant tools and materials will be delivered, utilised and removed per shift.&nbsp;</li>
	<li>As discussed with on site &nbsp;site management additional fire stopping to be confirmed and additional costs forwarded as encountered / required, existing penetrations are 450 x 150 for electrical containment at 5 number per room over 10 rooms as per issued scope to ensure safe working practices in relation to covid operatives will maintain contact but work in separate rooms and travel in separate vehicles, no allowance has been foreseen for parking costs as the client agreed GDC could park on site&nbsp;</li>
</ul>
