<p>it is assumed all agreed kitchen equipment will be removed prior to gdc attending site</p><p>all distribution board information and supply characteristics of building to be supplied by client.</p><p>new oven unit to be on site&nbsp;for measurements&nbsp;of service points etc (others to connect oven unit)</p><p>Electrical works</p><ul><li>operatives to attend site and sign in</li><li>all required isolations to be in place&nbsp;</li><li>Operatives to apply protective sheeting to work routes and working areas.</li><li>distribution board DB M53 to be isolated&nbsp;</li><li>commence with installing a 4mm 5 core cable from the distribution board to the new oven location</li><li>cable to be cable tied to existing containment where possible and run through stainless steel housing</li><li>new 16A 5 pin commando socket outlet with integral rcd protection to be installed to existing stainless steel housing</li><li>armoured cable to be terminated into new commando socket outlet ( all cables to be marked correctly and all terminations to be mechanically sound)</li><li>armoured cable to be terminated into distribution board</li><li>cables to be dressed to 3 phase breaker location</li><li>new 20A type c 3 phase breaker to be installed</li><li>circuit to have r1 +r2 tests carried out and results recorded</li><li>cirucit to be connected into new mcb and circuit energised</li><li>?all required live tests and fuctional tests to be carried out and results recorded.</li><li>site to be left clean and tidy</li></ul><p><strong>Plumbing works</strong></p><ul><li>operative to attend site and sign in</li><li>all required isolations to be in place</li><li>commence with installing water supply to new oven unit (15mm copper) pipe to be run along the floor level using uni strut and munson rings as agreed</li><li>to be connected to existing water supply and</li><li>a isolation valve and washing machine valve to be installed at the new oven location</li><li>new inch and a half copper waste to be installed from outlet of oven to existing tundish&nbsp;that falls into waste (copper tundish to be installed underneath over over spill outlet</li><li>15mm copper pipe to be lagged if required</li></ul><p>an O&amp;M manual to be provided on completion</p><p><strong>Our total cost to carry out the above works out of normal working hours shall be &pound;1,828.00+VAT</strong></p><p><strong>Breakdown</strong></p><p><strong>electrical Labour - &pound;386.00+VAT</strong></p><p><strong>Electrical material - &pound;551.00+VAT</strong></p><p><strong>Plumber Labour - &pound;386.00+VAT</strong></p><p><strong>Plumbing materials - &pound;250.00+VAT</strong></p><p><strong>O&amp;M manual - &pound;180.00+VAT</strong></p><p><strong>Protection - &pound;75.00+VAT</strong></p><p>&nbsp;</p><p>&nbsp;</p>