<p><strong>Ground Floor and 1st Floor Emergency Lighting upgrades.</strong></p><p><strong>Existing Emergency lights.&nbsp;</strong></p><p>With reference to survey carried out to the existing emergency lights,to provide a cost for upgrading and replacing for new. The existing lights consists of 17&nbsp;no emergency lights, 10 no non maintained lights and 7 maintained / sustained emergency lights. The 7 no. maintained / sustained emergency lights would remain as switch able lights, we would not replace these as this would mean the lights in those areas would not match existing, the only 2 we may change would be lights 5 &amp; 9 &nbsp;as on drawings due to being independent to the rest, or 2 new LED bulk head lights mounted adjacent to them.&nbsp;&nbsp;&nbsp;</p><p>Lights 1,2,6,7,8,12,14,17 as on drawing are to be replaced with LED bulk heads with 50 internal LED&#39;s self-test emergency non maintained lights.&nbsp;</p><p>Lights 10 and 11 on stairs, to be replaced for surface mounted self-test 28w 2D maintained/sustained wall mounted lights, LED lights for these are unavailable.&nbsp;</p><p><strong>Ground Floor additional lights ad rewiring of existing.&nbsp;</strong></p><p>Installation of 17 new LED bulk heads with 50 internal LED&#39;s self-test emergency non maintained lights.&nbsp;</p><p>4no. lights to 2 x disabled toilets, female toilets lobby and male toilets lobby are to be rewired through existing conduits, and new 28 watt 2D maintained / sustained self-test luminaries to be installed with local key switches.&nbsp;</p><p>4NO. lights to the shower room, female toilets, male toilets and boiler room are to be rewired through existing conduits, and new non maintained LED bulkhead self-test luminaire to be installed with local key switches. Due to not being available self-test emergency 5ft fluorescent&nbsp;lights, we would have to install LED bulk head lights.&nbsp;</p><p><strong>First floor additional lights and rewiring of existing.&nbsp;</strong></p><p>Installation of 11 new LED bulk heads with 50 internal LED&#39;s self-test emergency non maintained lights.&nbsp;</p><p>1no light to disabled toilet to be rewired through existing conduits, and new 28 watt 2D maintained / sustained self-test luminaire to be installed with local key switches.&nbsp;</p><p>1 No. light to the electrical intake cupboard to be rewired through existing conduits, and new non maintained LED bulk head self - test luminaire to be installed with local key switches. Due to not being available self-test emergency 5ft fluorescent lights, we would have to install LED bulk head light.</p><p><strong>Existing Electrical Installation Information.</strong></p><p>Existing installation consists of steel metal conduit installed in fabric of building with any additional wiring installed after the build wired in twin and earth cable above the false ceiling, each original light is connected via a 3 core flex onto a plug in rose, our installation will be wired using FP200&nbsp;white 1.5 2 core and earth, new lights to be installed and connected into the lighting circuits present in each area.&nbsp;</p><p>10 No. lights to be rewired through existing conduits, allowing a permanent live for connection to new emergency lights.&nbsp;</p><p>8.No lights to be replaced with new LED lights, presuming the original installation meets current regulations.&nbsp;</p><p>Our total cost to carry out the above works in normal working hours shall be &pound;11,233.00</p><p><strong>Breakdown:</strong></p><p>Labour: &pound;5,695.00</p><p>Materials: &pound;5,238.00</p><p>Electrical certificates: &pound;300.00</p>