<ul><li>Electrician attended site on 31st January to investigate why there is no power to the security cabin. &nbsp;</li><li>Electrician replaced burnt commando connection with rotary isolator also had to remove and replace tails going to consumer unit.</li><li>Site to be left clean and tidy.</li></ul><p><strong>Breakdown</strong></p><p>Labour: &pound;160.00</p><p>Materials: &pound;77.00</p><p>Our total cost to carry out the above works in&nbsp;normal working hours shall be</p>