<p><strong>AC WORKS TO LABS ONLY.</strong></p><p>Supply &amp; install Mitsubishi Heavy Industries air-conditioning systems based on heat load calculations.</p><p>Lab C25 (1.2kW) - 1no: 2.5kW Heat Pump (Cooling &amp; Heating) 4 Way Compact Cassette unit</p><p>&ldquo;served by&rdquo; outdoor unit floor standing, sited to roof space above.</p><p>Lab C2 (1.6kW) - 1no: 2.5kW Heat Pump (Cooling &amp; Heating) 4 Way Compact Cassette unit</p><p>&ldquo;served by&rdquo; outdoor unit floor standing, sited to roof space above.</p><p>5 YEAR PARTS WARRANTY INCLUDED*</p><p>*Warranty requires 6-monthly Planned Preventative Maintenance contract with GDC Building Services Ltd</p><p>Inverter systems quoted as they are more environmentally friendly lowering running costs &amp; extending system life.</p><p>Evaporator condensate drainage gravity to local waste or pumped to roof. Winter condensation of condenser drainage to ground, no pumps allowed for.</p><p>Control all via hard wired wall mounted remotes, cabling will be concealed where possible or within white PVC trunking.</p><p>Condenser 3no electrical supply/provision ( it is assumed that there is sufficient space within the local distribution board within the male toilet should it be proven there is not then the distribution board will need upgrading for an extra cost )to be supplied by us to condenser positions. Pipe work to be concealed internally where possible, we have allowed access hole to roof for pipe run, made good by us.</p><p>External pipework exposed (black in colour) &amp; interconnecting cabling will be mounted on cable tray installed by us.</p><p>Depth of cassettes are approx. 250mm.</p><p>Core drilling allowed for &amp; making good roofs.</p><p>Condensing units allowed to be manual handled to roof only, no cranage allowed for. Making good by us should we be doing builders works (separate quote).</p><p>Any license applications etc. are the duty of the client.</p><p>FGAS Certification included for within this quotation.</p><p><strong>Our total cost to carry out the above AC works&nbsp;out of hours shall cost - &pound;8,664.00+VAT</strong></p><p>&nbsp;</p><p><strong>AC WORKS TO SCI ADMIN OFFICE ONLY.</strong></p><p>Supply &amp; install Mitsubishi Heavy Industries air-conditioning systems based on heat load calculations.</p><p>SCI Administration (4.5kW) - 1no: 5kW Heat Pump (Cooling &amp; Heating) Wall Mount unit</p><p>&ldquo;served by&rdquo; outdoor unit floor standing, sited to roof space above.</p><p><strong>Our total cost to carry out the above AC works out of hours shall cost - &pound;5,354.00+VAT</strong></p><p>&nbsp;</p><p><strong>VENTILATION WORKS TO SCI ADMIN OFFICE</strong></p><p>Supply &amp; install supply &amp; extract ventilation to SCI Administration office based on 0.16 m3/s @ 100pa.</p><p>Supply air unit roof mounted to slab above on vibration mounts c/w. Panel filter.</p><p>Direct driven 3kW single stage fan. Electric heater battery.</p><p>Extract fan unit roof mounted to slab above on vibration mounts.</p><p>Both above systems controlled by bespoke HVAC control panel wall mounted within store room.</p><p>Duct routes through flat roof, diamond drilled 300mm supply, 200mm extract included in this cost is drilling &amp; making good to fiberglass finished roof.</p><p>Quote allows for 600x600mm white ceiling style Louvre boxes, including 4 way diffuser for supply &amp; low resistance return air louvre.</p><p>Quote allows for all insulated duct, transitions &amp; minimal flexible ducting to internal Louvre connections.</p><p>Spare way on distribution board required for electrical supply.</p><p>Any license applications etc. are the duty of the client.</p><p><strong>Our total cost to carry out the above ventilation works out of hours shall cost - &pound;7,880.00+VAT</strong></p><p>&nbsp;</p><p><strong>BUILDERS ELECTRICAL&nbsp;WORKS</strong></p><p>Paint finish to single colours&nbsp;as stated within spec.</p><p>Price allows for entry level commercial sanitary ware, trade budget items as required limited to above stated services unless stated.</p><p>Install&nbsp;Altro flooring throughout incl. skirting/upstands&nbsp;as stated within spec.</p><p>Including stainless steel sinks for labs incl. taps.</p><p>Including 6 double/double rads.</p><p>Including concealed toilet cisterns, urinal &amp; sink for male W.C.</p><p>Including Whiterock boarding for cleaners cupboard.</p><p>Including complete male W.C cubicles, fixtures &amp; fittings, incl. vanity unit &amp; concealed wall behind pans made from Trespa.</p><p>Including lighting as per YESSS lighting design, dimming to Labs only, other minor electrical works per tender spec.</p><p>Including LED lighting for W.C&rsquo;s &amp; store not depicted in YESSS lighting design.</p><p>Including W.C extract fans through the wall to cowl behind windows.</p><p>Freezing allowance to services where required.</p><p>CBRE isolations if required to be by site staff or any other costs for works not permitted by contractors not allowed for.</p><p>Diamond drilling/freezing/waste clearance weekend works.</p><p><strong>Our total cost to carry out the above builder and electrical works out of hours shall cost - &pound;51,571.00+VAT</strong></p><p><strong>PROJECT NOTES</strong></p><p>All isolations on site to be carried out by CBRE&nbsp;engineers.</p><p>As agreed onsite all waster and material transfers to be carried out on a weekend.</p><p>Diamond drilling to be carried out on a weekend.</p><p>Continual process of works, programme to be agreed with other parties.</p><p>should any down time be incurred it will be logged and an hourly rate of &pound;45.00+VAT will be charged.</p><p>the above cost does not include the lab work tops as we are unaware of the spec required.</p><p>we assumed that all wastes will run to a local stack as discussed on site.</p><p><strong>Our total cost to carry out all of works stated above is &pound;73,469.00+VAT</strong></p><p>&nbsp;</p>