<ul><li>Operatives to apply protective sheeting to work routes and working areas.</li><li>Operatives to carry out fire stopping and easement of doors as listed below.</li><li><p>Fire stopping required for any and all breaches in fire resisting walls, floors and ceilings caused by cabling, pipes etc. to maintain effective fire resistance between floors and compartments, this refers to;<br /><br />1. Common part services cupboards - breaches between floors and cables running into ceiling voids<br />2. Ground floor bin store - areas around door frame (unable to access adjacent bin store - check of fire resisting construction to be carried out)<br /><br />All breaches to be identified and a minimum of 1 hour fire stopping carried out.<br /><br />Please Check all fire exits in premises for general condition and operation.<br /><br />Examples of issues noted:<br /><br />1. Cupboard near flat 17 - combined intumescent strip and cold smoke seals missing<br />2. Third floor lift lobby to flat - combined intumescent strip and cold smoke seals missing<br />3. ground floor stair middle block - combined intumescent strip an cold smoke seals missing<br />4. First floor lobby to stair - fire door not closing effectively due to sound deadening pads being attached to the frames. Remove all pads and monitor for reintroduction</p></li><li>Site to be left clean and tidy.</li></ul><p>Our total cost to carry out the above works in&nbsp;normal working hours shall be &pound;3,183.00</p><p>Breakdown:</p><p>Labour: &pound;2,340.00</p><p>Materials: &pound;843.00</p>