<p><u><strong>1st Floor Landing exit - SWCP/009A</strong></u></p>

<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>Door to be adjusted.&nbsp;</li>
	<li>To supply &amp; install intumescent smoke seals.&nbsp;</li>
	<li>To supply &amp; install&nbsp;new drop seal.&nbsp;</li>
	<li>Site to be left clean and tidy.</li>
</ul>

<p><b><u>Ground Floor Front Door.&nbsp; - SWCP/010A/B</u></b></p>

<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>To supply &amp; install intumescent smoke seals.&nbsp;</li>
	<li>To carry out minor repair to the bottom of the door.&nbsp;</li>
	<li>Site to be left clean and tidy.</li>
</ul>

<p><b><u>Ground Floor Cleaners. - SWCP/011</u></b></p>

<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>Door to be adjusted.&nbsp;</li>
	<li>To supply &amp; install&nbsp;new drop seal.&nbsp;</li>
	<li>To supply &amp; instal fire signage.&nbsp;</li>
	<li>Site to be left clean and tidy.</li>
</ul>

<p><b><u>Ground Cafe exit. - SWCP/014A</u></b></p>

<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>Door to be adjusted.&nbsp;</li>
	<li>To supply &amp; install&nbsp;intumescent smoke seals.&nbsp;</li>
	<li>To supply &amp; install fire signage.&nbsp;</li>
	<li>Site to be left clean and tidy.</li>
</ul>

<p><b><u>Ground Cafe exit door 2. SWCP/015A/B</u></b></p>

<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>Door to be adjusted.&nbsp;</li>
	<li>To supply &amp; install&nbsp;intumescent smoke seals.&nbsp;</li>
	<li>To supply &amp; install fire signage.&nbsp;</li>
	<li>To re-secure the existing kick plates.&nbsp;</li>
	<li>To supply &amp; install new lock cover to existing lock.&nbsp;</li>
	<li>Site to be left clean and tidy.</li>
</ul>

<p><b><u>Ground Cafe exit door 3.-SWCP/016A</u></b></p>

<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>Door to be adjusted.&nbsp;</li>
	<li>To re-secure the existing kick plates.&nbsp;</li>
	<li>Site to be left clean and tidy.</li>
</ul>

<p><b><u>Ground Cafe side exit door.-SWCP/012A/B</u></b></p>

<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>To remove existing push bar set and dispose of.&nbsp;</li>
	<li>To supply &amp; install new push bar set.&nbsp;</li>
	<li>Check for correct working order.&nbsp;</li>
	<li>Site to be left clean and tidy.</li>
</ul>

<p><b><u>First Floor Hall to Landing door. -SWCP/008A/B</u></b></p>

<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>Door to be adjusted.&nbsp;</li>
	<li>To supply &amp; install&nbsp;intumescent smoke seals.&nbsp;</li>
	<li>To supply &amp; install fire door signage.&nbsp;</li>
	<li>Site to be left clean and tidy.</li>
</ul>

<p><b><u>Ground Floor Kitchen Door. -SWCP/013</u></b></p>

<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>Door to be adjusted.&nbsp;</li>
	<li>To&nbsp;supply &amp; install missing cover to around the handle.</li>
	<li>&nbsp;To supply &amp; install&nbsp;intumescent smoke seals.&nbsp;</li>
	<li>To supply &amp; install new door closer.&nbsp;</li>
	<li>To supply &amp; install fire door signage.&nbsp;</li>
	<li>Site to be left clean and tidy.</li>
</ul>

<p><b><u>First Floor Tea Point door.&nbsp; -SWCP/007</u></b></p>

<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>To remove existing door set and dispose of.&nbsp;</li>
	<li>To supply &amp; install new door set with intumscent seals, signage etc.&nbsp;</li>
	<li>Check for correct working order.</li>
	<li>All waste to be disposed of.&nbsp;</li>
	<li>Site to be left clean and tidy.</li>
</ul>

<p><b><u>First Floor Disabled WC.&nbsp; - SWCP/005</u></b></p>

<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>To adjust the frame.&nbsp;</li>
	<li>To supply &amp; install new drop seal.&nbsp;</li>
	<li>To supply &amp; install&nbsp;&nbsp;intumescent smoke seals.</li>
	<li>To adjust door closer.&nbsp;</li>
	<li>To supply &amp; install fire door signage.&nbsp;</li>
	<li>Site to be left clean and tidy.</li>
</ul>

<p><b><u>First Floor Store Room 2.&nbsp; -SWCP/004A</u></b></p>

<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>To ease and adjust the door.&nbsp;</li>
	<li>To supply &amp; install&nbsp;&nbsp;intumescent smoke seals.</li>
	<li>To supply &amp; install fire door signage.&nbsp;</li>
	<li>Site to be left clean and tidy.</li>
</ul>

<p><b><u>First Floor Store Room.&nbsp; -SWCP/003A</u></b></p>

<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>To adjust the door.&nbsp;</li>
	<li>To supply &amp; install&nbsp;&nbsp;intumescent smoke seals.</li>
	<li>To carry out minor repairs to the frame.&nbsp;</li>
	<li>To&nbsp;supply &amp; install fire door signage.&nbsp;</li>
	<li>Site to be left clean and tidy.</li>
</ul>

<p><b><u>Top Fire Exit.&nbsp; -SWCP/002A</u></b></p>

<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>To remove existing push bar set and dispose of.&nbsp;</li>
	<li>To supply &amp; install new push bar set.&nbsp;</li>
	<li>Check for correct working order.&nbsp;</li>
	<li>Site to be left clean and tidy.</li>
</ul>

<p><b><u>Top Fire Exit.&nbsp; -SWCP/001B</u></b></p>

<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>To supply &amp; install&nbsp;&nbsp;intumescent smoke seals.</li>
	<li>To&nbsp;supply &amp; install fire door signage.&nbsp;</li>
	<li>Site to be left clean and tidy.</li>
</ul>

<p><b><u>Ground Floor Gents Riser . -SWCP/018B</u></b></p>

<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>To ease and adjust the door.&nbsp;</li>
	<li>To supply &amp; install&nbsp;&nbsp;intumescent smoke seals.</li>
	<li>Site to be left clean and tidy.</li>
</ul>

<p><b><u>Ground Floor office exit.&nbsp; -SWCP/020</u></b></p>

<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>To&nbsp;supply &amp; install fire door signage.&nbsp;</li>
	<li>Site to be left clean and tidy.</li>
</ul>
