<p><u><strong>1st Floor 0003:06</strong></u></p>

<p><strong>Door Header - Non FIRAS Certified Works&nbsp;</strong></p>

<p>Asbestos insulation board is located above the existing mmmf insulation ceiling.</p>

<p>Supply and install a layer of 9mm thick Promat Supalux board to inside of door header within rider cupboard - approx 850 x 2150</p>

<p>Supply and fit 60mm thick Rockwool FirePro double coated ablative batt, all seams sealed with Rockwool FirePro Intumescent Acrylic Sealant and Rockwool FirePro ablative fire coat paint to seal void beneath existing damaged and non-compliant mineral fibre ceiling and around m&amp;e services penetrating fire compartment ceiling. Void size approx 450 x 2150</p>

<p><b>&pound;1,600 + Vat - 1 working shift/nights</b></p>

<p><b>1st Floor 0004:06 &amp; 0005:06</b></p>

<p>Asbestos insulation board is located along the entire head detail and would require removal to facilitate installation of FIRAS compliant fire protection (option 1)</p>

<p>Alternatively, the existing mineral fibre insulation abutting the AIB could be removed and the AIB enclosed/sealed and made safe to allow fire stopping of the exposed penetrations, however fire stopping onto asbestos could not be registered as compliant with FIRAS.</p>

<p><b>Option 1 - Asbestos Removal &amp; FIRAS Certified Works</b></p>

<p>Produce an ACoP compliant plan of works and submit a 14day ASB5 notification to the HSE. Locate and set up mobile decontamination units and the asbestos waste vehicle in the car park adjacent to the main entrance.</p>

<p>Asbestos trained operatives with RPE, PPE and specialist equipment to seal off the corridor adjacent to Pin 0005:06 to form an asbestos containment enclosure incorporating five stage waste/transit airlocks, negative pressure unit, vision panels &amp; cctv to monitor the works within the enclosure.</p>

<p>A smoke integrity test will be carried out to ensure an airtight seal has been achieved.</p>

<p>Remove and dispose of two rows of ceilings adjacent to the 10m long head detail, remove and dispose of containment mmmf insulation and the existing asbestos insulation board fire break.</p>

<p>Carry out an environmental clean of the entire enclosure using type H vacuum&nbsp;cleaners and tac-rags.</p>

<p>All waste to be taken to a licensed asbestos waste landfill site and a copy of the consignment note submitted for your records.</p>

<p>Periodic leak and personal air monitoring will be carried out whilst the works are in progress and on completion of the works an independent UKAS accredited analytical company will carry out a four stage clearance test, a copy of the reoccupation certificate will be submitted for your records.</p>

<p>Supply and fit 60mm thick Rockwool FirePro double coated ablative fire batt, all seams sealed with Rockwool FirePro Intumescent Acrylic Sealant and Rockwool FirePro ablative fire coat paint to head of wall above false ceiling. Size approx 450mm x 10LM</p>

<p><b>&pound;18,750 + Vat - Duration 7&nbsp;working shifts/nights</b></p>

<p><strong>Option 2 Encapsulation of Asbestos &amp; Non FIRAS&nbsp;Certified Works</strong></p>

<p>To supply asbestos trained operatives with RPE,PPE &amp; specialist equipment to remove the existing mineral fibre insulation abutting the asbestos insulation board (AIB), and enclosed/sealed and make safe the AIB panels, carry out a localised/precautionary environmental clean using a type H vacuum cleaner and tag rags.</p>

<p>All waste (including disposable PPE) to be taken to a licensed asbestos waste transfer station and a copy of the consignment note submitted for your records.</p>

<p>Arrange for an independent UKAS accredited analytical company to carry out reassurance air monitoring during / on completion of the works and submit a copy of the report for your records.</p>

<p>NB: The above works would be completed as short duration low intensity work with asbestos and would not require notification to the Health &amp; Safety Executive.</p>

<p>Supply and fit 60mm thick Rockwool FirePro double coated ablative fire batt, all seams sealed with Rockwool FirePro Intumescent Acrylic Sealant and Rockwool FirePro ablative fire coat paint, secured with Rockwool FirePro&nbsp;Glue screwed at bottom into block walls to seal voids and to seal around various m&amp;e service penetrations along the head of wall AIB insulation board above false ceiling.</p>

<p><strong>&pound;5,850 + Vat - 2 working shifts/nights</strong></p>

<p><strong>1st Floor 0006:06</strong></p>

<p>Asbestos insulation board is located above the penetrations - FIRAS Certified Works</p>

<p>Supply and fit 60mm thick Rockwool FirePro double coated ablative fire batt pattresses, all seams sealed with Rockwool FirePro Intumescent Acrylic Sealant &amp; Rockwool FirePro ablative fire coat paint to seal around pipework penetrating fire compartment wall above false ceiling.</p>

<p><strong>&pound;990 + Vat - 1 working shift/night</strong></p>

<p><strong>1st Floor 0007:06</strong></p>

<p>Asbestos insulation board is located above the penetrations - FIRAS Certified Works</p>

<p>Supply and fit 60mm thick Rockwool FirePro double coated ablative fire batt pattresses, all seams sealed with Rockwool FirePro Intumescent Acrylic Sealant &amp; Rockwool FirePro ablative fire coat paint to seal around pipework penetrating fire compartment wall above false ceiling.</p>

<p><strong>&pound;330&nbsp;+ Vat - 1 working shift/night</strong></p>

<p><strong>1st Floor 0008:06</strong></p>

<p>Asbestos insulation board is located along the head detail (5LM) above the fire doors and would require removal to facilitate installation of FIRAS compliant fire protection.</p>

<p>Alternatively, the existing asbestos insulation board could be&nbsp;enclosed/sealed and made safe to allow fire stopping of the exposed penetrations, however fire stopping onto asbestos could not be registered as compliant with FIRAS.</p>

<p><b>Option 1 - Asbestos Removal &amp; FIRAS Certified Works</b></p>

<p>Produce an ACoP compliant plan of works and submit a 14day ASB5 notification to the HSE. Locate and set up mobile decontamination units and the asbestos waste vehicle in the car park adjacent to the main entrance.</p>

<p>Asbestos trained operatives with RPE, PPE and specialist equipment to seal off the corridor adjacent to Pin 0008:06 to form an asbestos containment enclosure incorporating five stage waste/transit airlocks, negative pressure unit, vision panels &amp; cctv to monitor the works within the enclosure.</p>

<p>A smoke integrity test will be carried out to ensure an airtight seal has been achieved.</p>

<p>Remove and dispose of two rows of ceilings adjacent to the 5LM&nbsp;long head detail, remove and dispose of containment mmmf insulation and the existing asbestos insulation board fire break.</p>

<p>Carry out an environmental clean of the entire enclosure using type H vacuum&nbsp;cleaners and tac-rags.</p>

<p>All waste to be taken to a licensed asbestos waste landfill site and a copy of the consignment note submitted for your records.</p>

<p>Periodic leak and personal air monitoring will be carried out whilst the works are in progress and on completion of the works an independent UKAS accredited analytical company will carry out a four stage clearance test, a copy of the reoccupation certificate will be submitted for your records.</p>

<p>Supply and fit 60mm thick Rockwool FirePro double coated ablative fire batt, all seams sealed with Rockwool FirePro Intumescent Acrylic Sealant and Rockwool FirePro ablative fire coat paint to head of wall above false ceiling. Size approx 450mm x 5LM</p>

<p><strong>&pound;12,750 + Vat - 5 working shifts/nights</strong></p>

<p><strong>Option 2 Encapsulation of Asbestos &amp; Non FIRAS&nbsp;Certified Works</strong></p>

<p>To supply asbestos trained operatives with RPE,PPE &amp; specialist equipment to remove the existing mineral fibre insulation abutting the asbestos insulation board (AIB), and enclosed/sealed and make safe the AIB panels, carry out a localised/precautionary environmental clean using a type H vacuum cleaner and tag rags.</p>

<p>All waste (including disposable PPE) to be taken to a licensed asbestos waste transfer station and a copy of the consignment note submitted for your records.</p>

<p>Arrange for an independent UKAS accredited analytical company to carry out reassurance air monitoring during / on completion of the works and submit a copy of the report for your records.</p>

<p>NB: The above works would be completed as short duration low intensity work with asbestos and would not require notification to the Health &amp; Safety Executive.</p>

<p>Supply and fit 60mm thick Rockwool FirePro double coated ablative fire batt, all seams sealed with Rockwool FirePro Intumescent Acrylic Sealant and Rockwool FirePro ablative fire coat paint, secured with Rockwool FirePro&nbsp;Glue screwed at bottom into block walls to seal voids and to seal around various m&amp;e service penetrations along the head of wall AIB insulation board above false ceiling.</p>

<p><strong>&pound;4,500 + Vat - 2 working shifts/nights</strong></p>

<p><strong>1st Floor Pin 0009:06/ 0010:06 &amp; 0011:06</strong></p>

<p>Asbestos insulation board is located along the entire head detail and would require removal to facilitate installation of FIRAS compliant fire protection (option 1)</p>

<p>Alternatively, the existing mineral fibre insulation abutting the AIB could be removed and the AIB enclosed/sealed and made safe to allow fire stopping of the exposed penetrations, however fire stopping onto asbestos could not be registered as compliant with FIRAS.</p>

<p><b>Option 1 - Asbestos Removal &amp; FIRAS Certified Works</b></p>

<p>Produce an ACoP compliant plan of works and submit a 14day ASB5 notification to the HSE. Locate and set up mobile decontamination units and the asbestos waste vehicle in the car park adjacent to the main entrance.</p>

<p>Asbestos trained operatives with RPE, PPE and specialist equipment to seal off the corridor adjacent to Pin 0010:06 to form an asbestos containment enclosure incorporating five stage waste/transit airlocks, negative pressure unit, vision panels &amp; cctv to monitor the works within the enclosure.</p>

<p>A smoke integrity test will be carried out to ensure an airtight seal has been achieved.</p>

<p>Remove and dispose of two rows of ceilings adjacent to the 10m long head detail, remove and dispose of containment mmmf insulation and the existing asbestos insulation board fire break.</p>

<p>Carry out an environmental clean of the entire enclosure using type H vacuum&nbsp;cleaners and tac-rags.</p>

<p>All waste to be taken to a licensed asbestos waste landfill site and a copy of the consignment note submitted for your records.</p>

<p>Periodic leak and personal air monitoring will be carried out whilst the works are in progress and on completion of the works an independent UKAS accredited analytical company will carry out a four stage clearance test, a copy of the reoccupation certificate will be submitted for your records.</p>

<p>Supply and fit 60mm thick Rockwool FirePro double coated ablative fire batt, all seams sealed with Rockwool FirePro Intumescent Acrylic Sealant and Rockwool FirePro ablative fire coat paint to head of wall above false ceiling. Size approx 450mm x 10LM</p>

<p><b>&pound;18,750 + Vat - Duration 7&nbsp;working shifts/nights</b></p>

<p><strong>Option 2 Encapsulation of Asbestos &amp; Non FIRAS&nbsp;Certified Works</strong></p>

<p>To supply asbestos trained operatives with RPE,PPE &amp; specialist equipment to remove the existing mineral fibre insulation abutting the asbestos insulation board (AIB), and enclosed/sealed and make safe the AIB panels, carry out a localised/precautionary environmental clean using a type H vacuum cleaner and tag rags.</p>

<p>All waste (including disposable PPE) to be taken to a licensed asbestos waste transfer station and a copy of the consignment note submitted for your records.</p>

<p>Arrange for an independent UKAS accredited analytical company to carry out reassurance air monitoring during / on completion of the works and submit a copy of the report for your records.</p>

<p>NB: The above works would be completed as short duration low intensity work with asbestos and would not require notification to the Health &amp; Safety Executive.</p>

<p>Supply and fit 60mm thick Rockwool FirePro double coated ablative fire batt, all seams sealed with Rockwool FirePro Intumescent Acrylic Sealant and Rockwool FirePro ablative fire coat paint, secured with Rockwool FirePro&nbsp;Glue screwed at bottom into block walls to seal voids and to seal around various m&amp;e service penetrations along the head of wall AIB insulation board above false ceiling.</p>

<p><strong>&pound;5,850 + Vat - 2 working shifts/nights</strong></p>

<p><strong>1st Floor 0015:06</strong></p>

<p>Asbestos insulation board is located adjacent to the penetrations that require sealing - FIRAS Certified Works</p>

<p>Supply and fit 60mm thick Rockwool FirePro double coated ablative fire batt pattressess, all seams sealed with Rockwool FirePro Intumescent Acrylic Sealant and Rockwool FirePro ablative fire coat paint to seal head of wall across door set, approx 150x2100 above false ceiling.</p>

<p><strong>&pound;700 + Vat - 1 working shift/nights</strong></p>

<p><strong>1st Floor 0016:06, 0017:08 &amp; 0018:06</strong></p>

<p>Asbestos insulation board is located along the head detail above the fire doors and would need to be enclosed/sealed and made safe to allow fire stopping of the exposed penetrations.</p>

<p><strong>Encapsulation of Asbestos &amp; FIRAS Certified Works</strong></p>

<p>To supply asbestos trained operatives with RPE,PPE &amp; specialist equipment to remove the existing mineral fibre insulation abutting the asbestos insulation board (AIB), and enclosed/sealed and make safe the AIB panels, carry out a localised/precautionary environmental clean using a type H vacuum cleaner and tag rags.</p>

<p>All waste (including disposable PPE) to be taken to a licensed asbestos waste transfer station and a copy of the consignment note submitted for your records.</p>

<p>Arrange for an independent UKAS accredited analytical company to carry out reassurance air monitoring during / on completion of the works and submit a copy of the report for your records.</p>

<p>NB: The above works would be completed as short duration low intensity work with asbestos and would not require notification to the Health &amp; Safety Executive.</p>

<p>Supply and fit 60mm thick Rockwool FirePro double coated ablative fire batt pattresses, all seams sealed with Rockwool FirePro Intumescent Acrylic Sealant and Rockwool FirePro ablative fire coat paint to seal head of wall, approx 400x600 and supply and fit pattresses to seal around cables within riser.</p>

<p><strong>&pound;4,500 + Vat - 2 working shifts/nights</strong></p>

<p><strong>Ground Floor 0004:06</strong></p>

<p>Asbestos insulation board is located above the existing mmmf insulation ceiling - FIRAS Certified Works</p>

<p>Supply and fit 60mm thick Rockwool FirePro double coated ablative fire batt pattresses, all seams sealed with Rockwool FirePro Intumescent Acrylic Sealant and Rockwool FirePro ablative fire coat paint to seal around m&amp;e services above false ceiling.</p>

<p><strong>&pound;495 + Vat - 1 working shift/nights</strong></p>

<p><strong>Ground Floor 0005:06</strong></p>

<p>Asbestos insulation board is located above the existing mmmf insulation ceiling - FIRAS Certified Works</p>

<p>Supply and fit 60mm thick Rockwool FirePro double coated ablative fire batt pattresses, all seams sealed with Rockwool FirePro Intumescent Acrylic Sealant and Rockwool FirePro ablative fire coat paint to seal around m&amp;e services above false ceiling.</p>

<p><strong>&pound;495 + Vat - 1 working shift/nights</strong></p>

<p><strong>Ground Floor 0006:06&nbsp;</strong></p>

<p>Asbestos insulation board is located directly adjacent to the pipe penetrations and would need to be enclosed/sealed and made safe to allow fire stopping of the exposed penetrations.</p>

<p><strong>Encapsulation of Asbestos &amp; FIRAS Certified Works</strong></p>

<p>To supply asbestos trained operatives with RPE,PPE &amp; specialist equipment to enclosed/sealed and make safe the AIB panels, carry out a localised/precautionary environmental clean using a type H vacuum cleaner and tag rags.</p>

<p>All waste (including disposable PPE) to be taken to a licensed asbestos waste transfer station and a copy of the consignment note submitted for your records.</p>

<p>Arrange for an independent UKAS accredited analytical company to carry out reassurance air monitoring during / on completion of the works and submit a copy of the report for your records.</p>

<p>NB: The above works would be completed as short duration low intensity work with asbestos and would not require notification to the Health &amp; Safety Executive.</p>

<p>Supply and fit 60mm thick Rockwool FirePro double coated ablative fire batt pattresses, all seams sealed with Rockwool FirePro Intumescent Acrylic Sealant and Rockwool FirePro ablative fire coat paint to seal around m&amp;e services above false ceiling.</p>

<p><strong>&pound;3,150 + Vat - 2 Working shifts/nights</strong></p>

<p><strong>Ground Floor 0007:06</strong></p>

<p>Asbestos insulation board is located above the existing mmmf insulation ceiling - FIRAS Certified Works</p>

<p>Supply and fit 60mm thick Rockwool FirePro double coated ablative fire batt pattresses, all seams sealed with Rockwool FirePro Intumescent Acrylic Sealant and Rockwool FirePro ablative fire coat paint to seal head of wall,&nbsp;approx 100x5LM&nbsp;above false ceiling.</p>

<p><strong>&pound;1,475 + Vat - 1 Working Shift/Nights</strong></p>

<p><strong>Ground Floor 0009:06</strong></p>

<p>Asbestos insulation board is located along the entire head detail and would require removal to facilitate installation of FIRAS compliant fire protection.</p>

<p>Alternatively, the existing mineral fibre insulation abutting the AIB could be removed and the AIB enclosed/sealed and made safe to allow fire stopping of the exposed penetrations, however fire stopping onto asbestos could not be registered as compliant with FIRAS.</p>

<p><b>Option 1 - Asbestos Removal &amp; FIRAS Certified Works</b></p>

<p>Produce an ACoP compliant plan of works and submit a 14day ASB5 notification to the HSE. Locate and set up mobile decontamination units and the asbestos waste vehicle in the car park adjacent to the main entrance.</p>

<p>Asbestos trained operatives with RPE, PPE and specialist equipment to seal off the corridor adjacent to Pin 0009:06 to form an asbestos containment enclosure incorporating five stage waste/transit airlocks, negative pressure unit, vision panels &amp; cctv to monitor the works within the enclosure.</p>

<p>A smoke integrity test will be carried out to ensure an airtight seal has been achieved.</p>

<p>Remove and dispose of two rows of ceilings adjacent to the 6LM&nbsp;long head detail, remove and dispose of containment mmmf insulation and the existing asbestos insulation board fire break.</p>

<p>Carry out an environmental clean of the entire enclosure using type H vacuum&nbsp;cleaners and tac-rags.</p>

<p>All waste to be taken to a licensed asbestos waste landfill site and a copy of the consignment note submitted for your records.</p>

<p>Periodic leak and personal air monitoring will be carried out whilst the works are in progress and on completion of the works an independent UKAS accredited analytical company will carry out a four stage clearance test, a copy of the reoccupation certificate will be submitted for your records.</p>

<p>Supply and fit 60mm thick Rockwool FirePro double coated ablative fire batt, all seams sealed with Rockwool FirePro Intumescent Acrylic Sealant and Rockwool FirePro ablative fire coat paint to head of wall above false ceiling. Size approx 450mm x 6LM</p>

<p><b>&pound;16,550&nbsp;+ Vat - Duration 6&nbsp;working shifts/nights</b></p>

<p><strong>Option 2 Encapsulation of Asbestos &amp; Non FIRAS&nbsp;Certified Works</strong></p>

<p>To supply asbestos trained operatives with RPE,PPE &amp; specialist equipment to remove the existing mineral fibre insulation abutting the asbestos insulation board (AIB), and enclosed/sealed and make safe the AIB panels, carry out a localised/precautionary environmental clean using a type H vacuum cleaner and tag rags.</p>

<p>All waste (including disposable PPE) to be taken to a licensed asbestos waste transfer station and a copy of the consignment note submitted for your records.</p>

<p>Arrange for an independent UKAS accredited analytical company to carry out reassurance air monitoring during / on completion of the works and submit a copy of the report for your records.</p>

<p>NB: The above works would be completed as short duration low intensity work with asbestos and would not require notification to the Health &amp; Safety Executive.</p>

<p>Supply and fit 60mm thick Rockwool FirePro double coated ablative fire batt, all seams sealed with Rockwool FirePro Intumescent Acrylic Sealant and Rockwool FirePro ablative fire coat paint, secured with Rockwool FirePro&nbsp;Glue screwed at bottom into block walls to seal voids and to seal around various m&amp;e service penetrations along the head of wall AIB insulation board above false ceiling.</p>

<p><strong>&pound;5,750 + Vat - 2 working shifts/nights</strong></p>

<p><strong>Ground Floor 0010:06&nbsp;</strong></p>

<p><strong>Asbestos insulation board is located above the existing mmmf insulation ceiling - Non FIRAS Certified Works</strong></p>

<p>Supply and fit 60mm thick Rockwool FirePro double coated ablative fire batt, all seams sealed with Rockwool FirePro Intumescent Acrylic Sealant and Rockwool FirePro ablative fire coat paint to seal around ventilation ducting through wall. Cut out bottom section of ventilation ducting and supply and install an induct fusible link fire damper and galvanised steel access door into bottom of ducting, on completion make good and reseal galvanised steel ventilation ducting.</p>

<p>N.B. The approximate 500x500mm ventilation ducting would be restricted in size down to approx 360 x360mm due to the framework&nbsp;of the new internal induct fire damper.</p>

<p><strong>&pound;1,475 + Vat - 1 working shift/night</strong></p>

<p><strong>Ground Floor 0011:06</strong></p>

<p><strong>Asbestos insulation board is located above the existing mmmf insulation ceiling - FIRAS Certified Works</strong></p>

<p>Supply and fit 60mm thick Rockwool FirePro double coated ablative fire batt pattresses, all seams sealed with Rockwool FirePro Intumescent Acrylic Sealant and Rockwool FirePro ablative fire coat paint to seal around m&amp;e services above false ceiling.</p>

<p><b>&pound;880 + Vat - 1 working shift/nights</b></p>

<p><strong>Ground Floor 0012:06, 0013:06, 0014:06 &amp;&nbsp;0015:06</strong></p>

<p>Asbestos insulation board is located directly adjacent to the penetrations and would need to be enclosed/sealed and made safe to allow fire stopping of the exposed penetrations.</p>

<p><strong>Encapsulation of Asbestos &amp; FIRAS Certified Works</strong></p>

<p>To supply asbestos trained operatives with RPE,PPE and specialist equipment to enclosed/seal and make safe the AIB panels, carry out a localised/precautionary environmental clean using a type H vacuum cleaner and tac rags.</p>

<p>All waste (including disposable PPE) to be taken to a licensed asbestos waste transfer station and a copy of the consignment note submitted for your records.</p>

<p>Arrange for an independent UKAS accredited analytical company to carry out reassurance air monitoring during/on completion of the works and submit a copy of the report for your records.</p>

<p>N.B. The above works would be completed as short duration low intensity work with asbestos and would not require notification to the health &amp; safety executive.</p>

<p>Supply and fit 60mm thick Rockwool FirePro double coated ablative fire batt pattresses, all seams sealed with Rockwool FirePro intumescent Acrylic Sealant and Rockwool FirePro ablative fire coat paint to seal around m&amp;e services above false ceiling.</p>

<p><strong>&pound;4,500 + Vat - 2 working shifts/nights</strong></p>

<p><strong>Note :</strong></p>

<p>For all option 1 i.e licensed/notifiable removal of asbestos, we would require an area to locate our asbestos decontamination unit and asbestos waste collection vehicle with access to 240v power, mains water and a drainage point.</p>

<p>Decorative damage may occur during the enclosure construction, although we would endeavour to keep this to a minimum and the suspended ceiling may also require repair/replacement following licensed works. No allowance for these repairs (if required) have been made in our quotation,</p>

<p>Please be aware that for the durations stated for the licensed works, access would be completely restricted to the areas surrounding the asbestos containment enclosures, i.e these parts of the court would not be accessible for the full duration stated,</p>

<p>At this stage no allowance has been made for possible required works in adjacent areas during the option 1 licensed works i.e gaining access within the lift shafts etc for internal sealing or decontamination if required.</p>

<p>FIRAS Certified supervisor &amp; NVQ qualified passive fire protection engineers to carry out, label, record and certificate the above works.</p>

<p>All FIRAS works will be recorded, added to their FIRAS data base and before &amp; after photographic report provided for each individual seal number.</p>

<p>All Non-FIRAS works will be recorded, added to our data base and before and after photographic report produced&nbsp;for each individual seal number including in house completion certification.</p>

<p>The fire stopping will be installed in accordance with the manufacturers recommendations; a copy of Rockwool FirePro Installation Guide shall be submitted upon confirmation to proceed is received.</p>

<p>The above fire stopping application will provide the required fire rating as per information provided on the fire risk assessment.</p>

<p>&nbsp;</p>

<p>&nbsp;</p>
