<ul>
	<li>Operatives to apply protective sheeting to work routes and working areas.</li>
	<li>To isolate electrical supplies to existing faulty extract twin fan motor.</li>
	<li>To install temporary 110v lighting to W.C.</li>
	<li>To disconnect/isolate ceiling services such as lighting/smoke detector etc where not able to be temporarily located to one side of ceiling.</li>
	<li>To remove grid tiles and ceiling to accommodate access for removal/reinstallation of twin fans.</li>
	<li>To disconnect spigots/ ancillaries to permit lowering of existing faulty twin fan.&nbsp;</li>
	<li>To lower existing twin fan with CO2 gas genie lift &amp; cart away to van.</li>
	<li>To lift new twin fan with CO2 gas genie lift to final position.</li>
	<li>To connect spigots/ancillaries back up, including electrics &amp; test new twin fan.</li>
	<li>To reverse work process to replace ceiling/lights etc &amp; carry out house keeping.&nbsp;</li>
	<li>Site to be left clean and tidy.</li>
</ul>

<p><strong>Project Note: Please note, the direct replacement model for what we believe is the current twin fan is substantially larger than the current model, therefore we have sourced a similar design from a different manufacturer. The duty of the replacement fan is like-for-like &amp; superior to existing model from what believe the current model to be, the dimensions are extremely similar too, with only the height being less. We will provide a new &quot;changeover&quot; control module which will still work with the current HVAC control panel including clean-contracts fault monitoring/output. Existing spurs, pascal air-flow switches etc. as installed will be reused.&nbsp;</strong></p>
